Program Version:EnergyPlus, Version 9.1.0-08d2e308bb, YMD=2019.04.09 23:07
Tabular Output Report in Format: HTML
Building: -MediumOffice-ASHRAE 169-2006-5A created: 2018-10-22 12:11:34 -0600
Environment: RUN PERIOD 1 ** Chicago Ohare Intl Ap IL USA TMY3 WMO#=725300
Simulation Timestamp: 2019-04-09 23:07:32
Report: Annual Building Utility Performance Summary
For: Entire Facility
Timestamp: 2019-04-09 23:07:32
Values gathered over 8760.00 hours| Total Energy [GJ] | Energy Per Total Building Area [MJ/m2] | Energy Per Conditioned Building Area [MJ/m2] | |
| Total Site Energy | 1806.76 | 362.64 | 362.64 |
| Net Site Energy | 1806.76 | 362.64 | 362.64 |
| Total Source Energy | 5164.92 | 1036.68 | 1036.68 |
| Net Source Energy | 5164.92 | 1036.68 | 1036.68 |
| Site=>Source Conversion Factor | |
| Electricity | 3.167 |
| Natural Gas | 1.084 |
| District Cooling | 1.056 |
| District Heating | 3.613 |
| Steam | 0.300 |
| Gasoline | 1.050 |
| Diesel | 1.050 |
| Coal | 1.050 |
| Fuel Oil #1 | 1.050 |
| Fuel Oil #2 | 1.050 |
| Propane | 1.050 |
| Other Fuel 1 | 1.000 |
| Other Fuel 2 | 1.000 |
| Area [m2] | |
| Total Building Area | 4982.19 |
| Net Conditioned Building Area | 4982.19 |
| Unconditioned Building Area | 0.00 |
| Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | 0.00 | 173.23 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 247.80 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 338.04 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 105.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 763.69 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 73.03 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 1.11 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 10.45 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 94.22 | 0.00 | 0.00 | 0.00 | 278.19 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 1539.31 | 267.45 | 0.00 | 0.00 | 0.00 | 278.19 |
| Subcategory | Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | General | 0.00 | 173.23 | 0.00 | 0.00 | 0.00 | 0.00 |
| Boiler Parasitic | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Cooling | General | 247.80 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 338.04 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | General | 105.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 763.69 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 73.03 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 1.11 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 10.45 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | General | 0.00 | 94.22 | 0.00 | 0.00 | 0.00 | 278.19 |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 88.96 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 64.62 | 53.68 | 0.00 | 0.00 | 0.00 | 0.06 |
| Other | 155.38 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 308.96 | 53.68 | 0.00 | 0.00 | 0.00 | 0.06 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 88.96 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 64.62 | 53.68 | 0.00 | 0.00 | 0.00 | 0.06 |
| Other | 155.38 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 308.96 | 53.68 | 0.00 | 0.00 | 0.00 | 0.06 |
| Electricity [GJ] | Percent Electricity [%] | |
| Fuel-Fired Power Generation | 0.000 | 0.00 |
| High Temperature Geothermal* | 0.000 | 0.00 |
| Photovoltaic Power | 0.000 | 0.00 |
| Wind Power | 0.000 | 0.00 |
| Power Conversion | 0.000 | 0.00 |
| Net Decrease in On-Site Storage | 0.000 | 0.00 |
| Total On-Site Electric Sources | 0.000 | 0.00 |
| Electricity Coming From Utility | 1539.314 | 100.00 |
| Surplus Electricity Going To Utility | 0.000 | 0.00 |
| Net Electricity From Utility | 1539.314 | 100.00 |
| Total On-Site and Utility Electric Sources | 1539.314 | 100.00 |
| Total Electricity End Uses | 1539.314 | 100.00 |
| Heat [GJ] | Percent Heat [%] | |
| Water-Side Heat Recovery | 0.00 | 0.00 |
| Air to Air Heat Recovery for Cooling | 53.07 | 19.31 |
| Air to Air Heat Recovery for Heating | 221.75 | 80.69 |
| High-Temperature Geothermal* | 0.00 | 0.00 |
| Solar Water Thermal | 0.00 | 0.00 |
| Solar Air Thermal | 0.00 | 0.00 |
| Total On-Site Thermal Sources | 274.82 | 100.00 |
| Water [m3] | Percent Water [%] | |
| Rainwater Collection | 0.00 | 0.00 |
| Condensate Collection | 0.00 | 0.00 |
| Groundwater Well | 0.00 | 0.00 |
| Total On Site Water Sources | 0.00 | 0.00 |
| - | - | - |
| Initial Storage | 0.00 | 0.00 |
| Final Storage | 0.00 | 0.00 |
| Change in Storage | 0.00 | 0.00 |
| - | - | - |
| Water Supplied by Utility | 278.19 | 100.00 |
| - | - | - |
| Total On Site, Change in Storage, and Utility Water Sources | 278.19 | 100.00 |
| Total Water End Uses | 278.19 | 100.00 |
| Degrees [deltaC] | |
| Tolerance for Zone Heating Setpoint Not Met Time | 0.56 |
| Tolerance for Zone Cooling Setpoint Not Met Time | 0.56 |
| Facility [Hours] | |
| Time Setpoint Not Met During Occupied Heating | 292.50 |
| Time Setpoint Not Met During Occupied Cooling | 23.00 |
| Time Not Comfortable Based on Simple ASHRAE 55-2004 | 1062.33 |
Table of Contents
TopBUILDING ENERGY PERFORMANCE - ELECTRICITY
| Meter |BUILDING ENERGY PERFORMANCE - NATURAL GAS
| Meter |BUILDING ENERGY PERFORMANCE - ELECTRICITY PEAK DEMAND
| Meter |BUILDING ENERGY PERFORMANCE - NATURAL GAS PEAK DEMAND
| Meter |Life-Cycle Cost Report
| Entire Facility |Report: Input Verification and Results Summary
For: Entire Facility
Timestamp: 2019-04-09 23:07:32
General| Value | |
| Program Version and Build | EnergyPlus, Version 9.1.0-08d2e308bb, YMD=2019.04.09 23:07 |
| RunPeriod | RUN PERIOD 1 |
| Weather File | Chicago Ohare Intl Ap IL USA TMY3 WMO#=725300 |
| Latitude [deg] | 41.98 |
| Longitude [deg] | -87.9 |
| Elevation [m] | 201.00 |
| Time Zone | -6.0 |
| North Axis Angle [deg] | 0.00 |
| Rotation for Appendix G [deg] | 0.00 |
| Hours Simulated [hrs] | 8760.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Above Ground Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Window Opening Area [m2] | 652.83 | 195.85 | 130.57 | 195.85 | 130.57 |
| Gross Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Above Ground Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1369.16 | 410.75 | 273.83 | 410.75 | 273.83 |
| Above Ground Wall Area [m2] | 1369.16 | 410.75 | 273.83 | 410.75 | 273.83 |
| Window Opening Area [m2] | 652.83 | 195.85 | 130.57 | 195.85 | 130.57 |
| Gross Window-Wall Ratio [%] | 47.68 | 47.68 | 47.68 | 47.68 | 47.68 |
| Above Ground Window-Wall Ratio [%] | 47.68 | 47.68 | 47.68 | 47.68 | 47.68 |
| Total | |
| Gross Roof Area [m2] | 1660.73 |
| Skylight Area [m2] | 0.00 |
| Skylight-Roof Ratio [%] | 0.00 |
| Area [m2] | Conditioned (Y/N) | Part of Total Floor Area (Y/N) | Volume [m3] | Multipliers | Above Ground Gross Wall Area [m2] | Underground Gross Wall Area [m2] | Window Glass Area [m2] | Opening Area [m2] | Lighting [W/m2] | People [m2 per person] | Plug and Process [W/m2] | |
| CORE_BOTTOM ZN | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 8.8264 | 18.58 | 40.8492 |
| CORE_MID ZN | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 8.8264 | 18.58 | 8.0729 |
| CORE_TOP ZN | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 8.8264 | 18.58 | 8.0729 |
| FIRSTFLOOR_PLENUM ZN | 1660.73 | No | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| MIDFLOOR_PLENUM ZN | 1660.73 | No | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| PERIMETER_BOT_ZN_1 ZN | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_BOT_ZN_2 ZN | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_BOT_ZN_3 ZN | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_BOT_ZN_4 ZN | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_MID_ZN_1 ZN | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_MID_ZN_2 ZN | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_MID_ZN_3 ZN | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_MID_ZN_4 ZN | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_TOP_ZN_1 ZN | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_TOP_ZN_2 ZN | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_TOP_ZN_3 ZN | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_TOP_ZN_4 ZN | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 8.8264 | 18.58 | 8.0729 |
| TOPFLOOR_PLENUM ZN | 1660.73 | No | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| Total | 4982.19 | 13667.13 | 1369.16 | 0.00 | 652.83 | 652.83 | 8.8264 | 18.58 | 14.5433 | |||
| Conditioned Total | 4982.19 | 13667.13 | 1369.16 | 0.00 | 652.83 | 652.83 | 8.8264 | 18.58 | 14.5433 | |||
| Unconditioned Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | ||||||
| Not Part of Total | 4982.19 | 6074.28 | 608.51 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 |
Report: Demand End Use Components Summary
For: Entire Facility
Timestamp: 2019-04-09 23:07:32
End Uses| Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Time of Peak | 11-JUL-12:00 | 30-JAN-07:40 | - | - | - | 02-JAN-12:09 |
| Heating | 0.00 | 263380.88 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 88500.25 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 26850.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 49974.15 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 22804.24 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 16.15 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 8160.93 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 188144.98 | 271541.81 | 0.00 | 0.00 | 0.00 | 0.00 |
| Subcategory | Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Heating | General | 0.00 | 263380.88 | 0.00 | 0.00 | 0.00 | 0.00 |
| Boiler Parasitic | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Cooling | General | 88500.25 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 26850.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 49974.15 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 22804.24 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 16.15 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | General | 0.00 | 8160.93 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Source Energy End Use Components Summary
For: Entire Facility
Timestamp: 2019-04-09 23:07:32
Values gathered over 8760.00 hours| Source Electricity [GJ] | Source Natural Gas [GJ] | Source Additional Fuel [GJ] | Source District Cooling [GJ] | Source District Heating [GJ] | |
| Heating | 0.00 | 187.78 | 0.00 | 0.00 | 0.00 |
| Cooling | 784.78 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 1070.59 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 333.14 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 2418.61 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 231.30 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 3.50 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 33.09 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 102.13 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 4875.01 | 289.91 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 0.00 | 37.69 | 0.00 | 0.00 | 0.00 |
| Cooling | 157.52 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 214.88 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 66.87 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 485.45 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 46.42 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.70 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 6.64 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 20.50 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 978.49 | 58.19 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 0.00 | 37.69 | 0.00 | 0.00 | 0.00 |
| Cooling | 157.52 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 214.88 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 66.87 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 485.45 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 46.42 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.70 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 6.64 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 20.50 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 978.49 | 58.19 | 0.00 | 0.00 | 0.00 |
Report: Component Sizing Summary
For: Entire Facility
Timestamp: 2019-04-09 23:07:32
AirTerminal:SingleDuct:VAV:Reheat| Design Size Maximum Air Flow Rate [m3/s] | Design Size Constant Minimum Air Flow Fraction | User-Specified Constant Minimum Air Flow Fraction | Design Size Minimum Air Flow Rate [m3/s] | Design Size Maximum Flow Fraction during Reheat [] | User-Specified Maximum Flow Fraction during Reheat [] | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | Design Size Maximum Reheat Water Flow Rate [m3/s] | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | |
| CORE_BOTTOM ZN VAV TERMINAL | 3.11 | 0.240968 | 0.100000 | 0.311018 | 0.642582 | 0.500000 | 0.001581 | 0.000252 | 0.348828 | 12.78 | 0.008000 |
| CORE_MID ZN VAV TERMINAL | 2.30 | 0.325962 | 0.100000 | 0.229921 | 0.869233 | 0.500000 | 0.001169 | 0.000467 | 0.648856 | 12.78 | 0.008000 |
| CORE_TOP ZN VAV TERMINAL | 2.32 | 0.322649 | 0.100000 | 0.232281 | 0.860398 | 0.500000 | 0.001181 | 0.000843 | 1.17 | 12.78 | 0.008000 |
| PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | 0.805111 | 0.196236 | 0.100000 | 0.080511 | 0.523296 | 0.500000 | 0.001942 | 0.000269 | 0.374754 | 12.78 | 0.008000 |
| PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | 0.789446 | 0.126699 | 0.100000 | 0.078945 | 0.337863 | 0.500000 | 0.003007 | 0.000175 | 0.243906 | 12.78 | 0.008000 |
| PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | 0.501406 | 0.315097 | 0.100000 | 0.050141 | 0.840259 | 0.500000 | 0.001209 | 0.000264 | 0.367625 | 12.78 | 0.008000 |
| PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | 0.799286 | 0.125131 | 0.100000 | 0.079929 | 0.333682 | 0.500000 | 0.003045 | 0.000178 | 0.247840 | 12.78 | 0.008000 |
| PERIMETER_MID_ZN_1 ZN VAV TERMINAL | 0.919973 | 0.171735 | 0.100000 | 0.091997 | 0.457960 | 0.500000 | 0.002219 | 0.000321 | 0.447365 | 12.78 | 0.008000 |
| PERIMETER_MID_ZN_2 ZN VAV TERMINAL | 0.873075 | 0.114563 | 0.100000 | 0.087308 | 0.305500 | 0.500000 | 0.003326 | 0.000208 | 0.289984 | 12.78 | 0.008000 |
| PERIMETER_MID_ZN_3 ZN VAV TERMINAL | 0.610925 | 0.258611 | 0.100000 | 0.061092 | 0.689628 | 0.500000 | 0.001473 | 0.000316 | 0.441090 | 12.78 | 0.008000 |
| PERIMETER_MID_ZN_4 ZN VAV TERMINAL | 0.875929 | 0.114182 | 0.100000 | 0.087593 | 0.304485 | 0.500000 | 0.003337 | 0.000211 | 0.294569 | 12.78 | 0.008000 |
| PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | 0.987346 | 0.160017 | 0.100000 | 0.098735 | 0.426711 | 0.500000 | 0.002381 | 0.000396 | 0.553216 | 12.78 | 0.008000 |
| PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | 0.874807 | 0.114336 | 0.100000 | 0.087481 | 0.304896 | 0.500000 | 0.003332 | 0.000256 | 0.356862 | 12.78 | 0.008000 |
| PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | 0.686559 | 0.230121 | 0.100000 | 0.068656 | 0.613656 | 0.500000 | 0.001656 | 0.000393 | 0.548154 | 12.78 | 0.008000 |
| PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | 0.921668 | 0.108515 | 0.100000 | 0.092167 | 0.300000 | 0.500000 | 0.003511 | 0.000259 | 0.361618 | 12.78 | 0.008000 |
| Design Size Rated Capacity [W] | Design Size Maximum Water Flow Rate [m3/s] | Design Size U-Factor Times Area Value [W/K] | |
| CORE_BOTTOM ZN REHEAT COIL | 11539.36 | 0.000252 | 837.19 |
| CORE_MID ZN REHEAT COIL | 21364.57 | 0.000467 | 1539.10 |
| CORE_TOP ZN REHEAT COIL | 38532.06 | 0.000843 | 2762.86 |
| PERIMETER_BOT_ZN_1 ZN REHEAT COIL | 12284.87 | 0.000269 | 879.10 |
| PERIMETER_BOT_ZN_2 ZN REHEAT COIL | 7995.01 | 0.000175 | 572.07 |
| PERIMETER_BOT_ZN_3 ZN REHEAT COIL | 12051.70 | 0.000264 | 862.48 |
| PERIMETER_BOT_ZN_4 ZN REHEAT COIL | 8123.66 | 0.000178 | 581.24 |
| PERIMETER_MID_ZN_1 ZN REHEAT COIL | 14659.21 | 0.000321 | 1048.38 |
| PERIMETER_MID_ZN_2 ZN REHEAT COIL | 9501.72 | 0.000208 | 679.48 |
| PERIMETER_MID_ZN_3 ZN REHEAT COIL | 14453.99 | 0.000316 | 1033.74 |
| PERIMETER_MID_ZN_4 ZN REHEAT COIL | 9651.66 | 0.000211 | 690.17 |
| PERIMETER_TOP_ZN_1 ZN REHEAT COIL | 18121.06 | 0.000396 | 1295.25 |
| PERIMETER_TOP_ZN_2 ZN REHEAT COIL | 11688.93 | 0.000256 | 835.45 |
| PERIMETER_TOP_ZN_3 ZN REHEAT COIL | 17955.52 | 0.000393 | 1283.44 |
| PERIMETER_TOP_ZN_4 ZN REHEAT COIL | 11844.45 | 0.000259 | 846.54 |
| 15 ZONE VAV MAIN HTG COIL | 63968.66 | 0.001399 | 1855.29 |
| Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | Sum of Air Terminal Maximum Flow Rates [m3/s] | Adjusted Heating Design Air Flow Rate [m3/s] | Adjusted Cooling Design Air Flow Rate [m3/s] | Adjusted Main Design Air Flow Rate [m3/s] | User Heating Air Flow Ratio [] | Calculated Heating Air Flow Ratio [] | Design Supply Air Flow Rate [m3/s] | |
| 15 ZONE VAV | 8.69 | 1.74 | 17.38 | 6.77 | 14.76 | 14.76 | 0.300000 | 0.458859 | 14.76 |
| Maximum Outdoor Air Flow Rate [m3/s] | |
| 15 ZONE VAV OA CONTROLLER | 14.76 |
| Design Size Nominal Supply Air Flow Rate [m3/s] | |
| 15 ZONE VAV ERV | 2.15 |
| Design Size High Speed Rated Air Flow Rate [m3/s] | Design Size High Speed Gross Rated Total Cooling Capacity [W] | Design Size High Speed Rated Sensible Heat Ratio | Design Size Low Speed Rated Air Flow Rate [m3/s] | Design Size Low Speed Gross Rated Total Cooling Capacity [W] | Design Size Low Speed Gross Rated Sensible Heat Ratio | User-Specified Low Speed Gross Rated Sensible Heat Ratio | |
| 15 ZONE VAV 2SPD DX CLG COIL | 14.76 | 299069.81 | 0.767436 | 4.92 | 99679.97 | 0.767436 | 0.690000 |
| Design Size Maximum Flow Rate [m3/s] | |
| 15 ZONE VAV FAN | 14.76 |
| Maximum Actuated Flow [m3/s] | |
| 15 ZONE VAV MAIN HTG COIL CONTROLLER | 0.001399 |
| Maximum Loop Flow Rate [m3/s] | Plant Loop Volume [m3] | |
| HOT WATER LOOP | 0.006206 | 0.744735 |
| MAIN SERVICE WATER LOOP | 0.000054 | 0.006435 |
| Design Flow Rate [m3/s] | Design Power Consumption [W] | |
| HOT WATER LOOP PUMP | 0.006206 | 1869.01 |
| Design Size Nominal Capacity [W] | Design Size Design Water Flow Rate [m3/s] | |
| BOILER 968KBTU/HR 0.94 COMBUSTION EFF | 283736.43 | 0.006206 |
| Design Flow Rate [m3/s] | Design Power Consumption [W] | |
| SERVICE WATER LOOP PUMP | 0.000054 | 16.15 |
| Use Side Design Flow Rate [m3/s] | |
| 100GAL NATURAL GAS WATER HEATER - 100KBTU/HR 0.802 THERM EFF 0.808 THERM EFF | 0.000054 |
Report: Surface Shadowing Summary
For: Entire Facility
Timestamp: 2019-04-09 23:07:32
Surfaces (Walls, Roofs, etc) that may be Shadowed by Other Surfaces| None |
| Possible Shadow Receivers | |
| PERIMETER_BOT_ZN_1_WALL_SOUTH | PERIMETER_BOT_ZN_1_WALL_SOUTH_WINDOW | |
| PERIMETER_BOT_ZN_2_WALL_EAST | PERIMETER_BOT_ZN_2_WALL_EAST_WINDOW | |
| PERIMETER_BOT_ZN_3_WALL_NORTH | PERIMETER_BOT_ZN_3_WALL_NORTH_WINDOW | |
| PERIMETER_BOT_ZN_4_WALL_WEST | PERIMETER_BOT_ZN_4_WALL_WEST_WINDOW | |
| PERIMETER_MID_ZN_1_WALL_SOUTH | PERIMETER_MID_ZN_1_WALL_SOUTH_WINDOW | |
| PERIMETER_MID_ZN_2_WALL_EAST | PERIMETER_MID_ZN_2_WALL_EAST_WINDOW | |
| PERIMETER_MID_ZN_3_WALL_NORTH | PERIMETER_MID_ZN_3_WALL_NORTH_WINDOW | |
| PERIMETER_MID_ZN_4_WALL_WEST | PERIMETER_MID_ZN_4_WALL_WEST_WINDOW | |
| PERIMETER_TOP_ZN_1_WALL_SOUTH | PERIMETER_TOP_ZN_1_WALL_SOUTH_WINDOW | |
| PERIMETER_TOP_ZN_2_WALL_EAST | PERIMETER_TOP_ZN_2_WALL_EAST_WINDOW | |
| PERIMETER_TOP_ZN_3_WALL_NORTH | PERIMETER_TOP_ZN_3_WALL_NORTH_WINDOW | |
| PERIMETER_TOP_ZN_4_WALL_WEST | PERIMETER_TOP_ZN_4_WALL_WEST_WINDOW | |
Report: Adaptive Comfort Summary
For: Entire Facility
Timestamp: 2019-04-09 23:07:32
Time Not Meeting the Adaptive Comfort Models during Occupied Hours| ASHRAE55 90% Acceptability Limits [Hours] | ASHRAE55 80% Acceptability Limits [Hours] | CEN15251 Category I Acceptability Limits [Hours] | CEN15251 Category II Acceptability Limits [Hours] | CEN15251 Category III Acceptability Limits [Hours] |
Report: Initialization Summary
For: Entire Facility
Timestamp: 2019-04-09 23:07:32
Version| Version ID | |
| 1 | 9.1 |
| #TimeSteps | Minutes per TimeStep {minutes} | |
| 1 | 6 | 10 |
| Minimum System TimeStep {minutes} | Max HVAC Iterations | Minimum Plant Iterations | Maximum Plant Iterations | |
| 1 | 2 | 25 | 2 | 8 |
| Do Zone Sizing | Do System Sizing | Do Plant Sizing | Do Design Days | Do Weather Simulation | Do HVAC Sizing Simulation | |
| 1 | Yes | Yes | Yes | No | Yes | No |
| Tolerance for Time Heating Setpoint Not Met | Tolerance for Zone Cooling Setpoint Not Met Time | |
| 1 | 0.556 | 0.556 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 20.49 | 20.43 | 20.44 | 20.50 | 20.59 | 22.83 | 23.24 | 23.33 | 23.36 | 21.14 | 20.78 | 20.61 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | -1.89 | -3.06 | -0.99 | 2.23 | 10.68 | 17.20 | 21.60 | 22.94 | 20.66 | 15.60 | 8.83 | 2.56 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Normal | Daylighting {dimensionless} | |
| 1 | 1.000 | 1.000 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Wind Sensor Height Above Ground {m} | Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Sensor Height Above Ground {m} | Wind Speed Modifier Coefficient-Internal | Temperature Modifier Coefficient-Internal | |
| 1 | 10.000 | 0.140 | 270.000 | 1.500 | 1.586 | 9.750E-003 |
| Location Name | Latitude {N+/S- Deg} | Longitude {E+/W- Deg} | Time Zone Number {GMT+/-} | Elevation {m} | Standard Pressure at Elevation {Pa} | Standard RhoAir at Elevation | |
| 1 | Chicago Ohare Intl Ap IL USA TMY3 WMO#=725300 | 41.98 | -87.92 | -6.00 | 201.00 | 98934 | 1.1759 |
| Calculation Method{} | Water Mains Temperature Schedule Name{} | Annual Average Outdoor Air Temperature{C} | Maximum Difference In Monthly Average Outdoor Air Temperatures{deltaC} | Fixed Default Water Mains Temperature{C} | |
| 1 | Correlation | NA | 9.93 | 28.70 | NA |
| Building Name | North Axis {deg} | Terrain | Loads Convergence Tolerance Value | Temperature Convergence Tolerance Value | Solar Distribution | Maximum Number of Warmup Days | Minimum Number of Warmup Days | |
| 1 | -MediumOffice-ASHRAE 169-2006-5A created: 2018-10-22 12:11:34 -0600 | 0.000 | City | 4.00000E-002 | 0.20000 | FullInteriorAndExterior | 25 | 6 |
| Algorithm {Simple TARP CeilingDiffuser AdaptiveConvectionAlgorithm} |
|
| 1 | TARP |
| Algorithm {SimpleCombined TARP MoWitt DOE-2 AdaptiveConvectionAlgorithm} |
|
| 1 | TARP |
| Value {Anisotropic} | |
| 1 | Anisotropic |
| Value {ThirdOrderBackwardDifference AnalyticalSolution EulerMethod} |
|
| 1 | ThirdOrderBackwardDifference |
| Simulation {Yes/No} | Carbon Dioxide Concentration | |
| 1 | No | N/A |
| Simulation {Yes/No} | Generic Contaminant Concentration | |
| 1 | No | N/A |
| Enforce Mass Balance |
Adjust Zone Mixing |
Adjust Zone Infiltration {AddInfiltration AdjustInfiltration None} |
Infiltration Zones {MixingSourceZonesOnly AllZones} |
|
| 1 | No | N/A | N/A | N/A |
| Value {RegulaFalsi Bisection BisectionThenRegulaFalsi RegulaFalsiThenBisection} |
|
| 1 | RegulaFalsi |
| Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Gradient Coefficient {K/m} | |
| 1 | 0.330 | 460.000 | 6.500000E-003 |
| Starting Corner | Vertex Input Direction | Coordinate System | Daylight Reference Point Coordinate System | Rectangular (Simple) Surface Coordinate System | |
| 1 | UpperLeftCorner | Counterclockwise | RelativeCoordinateSystem | RelativeCoordinateSystem | RelativeToZoneOrigin |
| Value {CTF - ConductionTransferFunction EMPD - MoisturePenetrationDepthConductionTransferFunction CondFD - ConductionFiniteDifference HAMT - CombinedHeatAndMoistureFiniteElement} - Description |
Inside Surface Max Temperature Limit{C} |
Surface Convection Coefficient Lower Limit {W/m2-K} |
Surface Convection Coefficient Upper Limit {W/m2-K} |
|
| 1 | CTF - ConductionTransferFunction | 200 | 0.10 | 1000.0 |
| Number of Fixed Detached Shades | Number of Building Detached Shades | Number of Attached Shades | |
| 1 | 0 | 0 | 0 |
| Number of Zones | Number of Zone Surfaces | Number of SubSurfaces | |
| 1 | 18 | 155 | 12 |
| Zone Name | North Axis {deg} | Origin X-Coordinate {m} | Origin Y-Coordinate {m} | Origin Z-Coordinate {m} | Centroid X-Coordinate {m} | Centroid Y-Coordinate {m} | Centroid Z-Coordinate {m} | Type | Zone Multiplier | Zone List Multiplier | Minimum X {m} | Maximum X {m} | Minimum Y {m} | Maximum Y {m} | Minimum Z {m} | Maximum Z {m} | Ceiling Height {m} | Volume {m3} | Zone Inside Convection Algorithm {Simple-Detailed-CeilingDiffuser-TrombeWall} | Zone Outside Convection Algorithm {Simple-Detailed-Tarp-MoWitt-DOE-2-BLAST} | Floor Area {m2} | Exterior Gross Wall Area {m2} | Exterior Net Wall Area {m2} | Exterior Window Area {m2} | Number of Surfaces | Number of SubSurfaces | Number of Shading SubSurfaces | Part of Total Building Area | |
| 1 | CORE_BOTTOM ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 1.37 | 1 | 1 | 1 | 4.57 | 45.34 | 4.57 | 28.70 | 0.00 | 2.74 | 2.74 | 2698.04 | TARP | TARP | 983.54 | 0.00 | 0.00 | 0.00 | 6 | 0 | 0 | Yes |
| 2 | CORE_MID ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 5.33 | 1 | 1 | 1 | 4.57 | 45.34 | 4.57 | 28.70 | 3.96 | 6.71 | 2.74 | 2698.04 | TARP | TARP | 983.54 | 0.00 | 0.00 | 0.00 | 6 | 0 | 0 | Yes |
| 3 | CORE_TOP ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 9.30 | 1 | 1 | 1 | 4.57 | 45.34 | 4.57 | 28.70 | 7.92 | 10.67 | 2.74 | 2698.04 | TARP | TARP | 983.54 | 0.00 | 0.00 | 0.00 | 6 | 0 | 0 | Yes |
| 4 | FIRSTFLOOR_PLENUM ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 3.35 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 33.27 | 2.74 | 3.96 | 1.22 | 2024.76 | TARP | TARP | 1660.73 | 202.84 | 202.84 | 0.00 | 14 | 0 | 0 | No |
| 5 | MIDFLOOR_PLENUM ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 7.32 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 33.27 | 6.71 | 7.92 | 1.22 | 2024.76 | TARP | TARP | 1660.73 | 202.84 | 202.84 | 0.00 | 14 | 0 | 0 | No |
| 6 | PERIMETER_BOT_ZN_1 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 2.16 | 1.37 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 4.57 | 0.00 | 2.74 | 2.74 | 568.77 | TARP | TARP | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 7 | PERIMETER_BOT_ZN_2 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 47.82 | 16.64 | 1.37 | 1 | 1 | 1 | 45.34 | 49.91 | 0.00 | 33.27 | 0.00 | 2.74 | 2.74 | 360.08 | TARP | TARP | 131.26 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 8 | PERIMETER_BOT_ZN_3 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 31.11 | 1.37 | 1 | 1 | 1 | 0.00 | 49.91 | 28.70 | 33.27 | 0.00 | 2.74 | 2.74 | 568.77 | TARP | TARP | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 9 | PERIMETER_BOT_ZN_4 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 2.09 | 16.64 | 1.37 | 1 | 1 | 1 | 0.00 | 4.57 | 0.00 | 33.27 | 0.00 | 2.74 | 2.74 | 360.05 | TARP | TARP | 131.25 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 10 | PERIMETER_MID_ZN_1 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 2.16 | 5.33 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 4.57 | 3.96 | 6.71 | 2.74 | 568.77 | TARP | TARP | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 11 | PERIMETER_MID_ZN_2 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 47.82 | 16.64 | 5.33 | 1 | 1 | 1 | 45.34 | 49.91 | 0.00 | 33.27 | 3.96 | 6.71 | 2.74 | 360.08 | TARP | TARP | 131.26 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 12 | PERIMETER_MID_ZN_3 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 31.11 | 5.33 | 1 | 1 | 1 | 0.00 | 49.91 | 28.70 | 33.27 | 3.96 | 6.71 | 2.74 | 568.77 | TARP | TARP | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 13 | PERIMETER_MID_ZN_4 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 2.09 | 16.64 | 5.33 | 1 | 1 | 1 | 0.00 | 4.57 | 0.00 | 33.27 | 3.96 | 6.71 | 2.74 | 360.05 | TARP | TARP | 131.25 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 14 | PERIMETER_TOP_ZN_1 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 2.16 | 9.30 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 4.57 | 7.92 | 10.67 | 2.74 | 568.77 | TARP | TARP | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 15 | PERIMETER_TOP_ZN_2 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 47.82 | 16.64 | 9.30 | 1 | 1 | 1 | 45.34 | 49.91 | 0.00 | 33.27 | 7.92 | 10.67 | 2.74 | 360.08 | TARP | TARP | 131.26 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 16 | PERIMETER_TOP_ZN_3 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 31.11 | 9.30 | 1 | 1 | 1 | 0.00 | 49.91 | 28.70 | 33.27 | 7.92 | 10.67 | 2.74 | 568.77 | TARP | TARP | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 17 | PERIMETER_TOP_ZN_4 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 2.09 | 16.64 | 9.30 | 1 | 1 | 1 | 0.00 | 4.57 | 0.00 | 33.27 | 7.92 | 10.67 | 2.74 | 360.05 | TARP | TARP | 131.25 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 18 | TOPFLOOR_PLENUM ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 11.28 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 33.27 | 10.67 | 11.89 | 1.22 | 2024.76 | TARP | TARP | 1660.73 | 202.84 | 202.84 | 0.00 | 10 | 0 | 0 | No |
| Zone Name | Floor Area {m2} | # Occupants | Area per Occupant {m2/person} | Occupant per Area {person/m2} | Interior Lighting {W/m2} | Electric Load {W/m2} | Gas Load {W/m2} | Other Load {W/m2} | Hot Water Eq {W/m2} | Steam Equipment {W/m2} | Sum Loads per Area {W/m2} | Outdoor Controlled Baseboard Heat | |
| 1 | CORE_BOTTOM ZN | 983.54 | 52.9 | 18.581 | 5.382E-002 | 8.826 | 40.849 | 0.000 | 0.000 | 0.000 | 0.000 | 49.676 | No |
| 2 | CORE_MID ZN | 983.54 | 52.9 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 3 | CORE_TOP ZN | 983.54 | 52.9 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 4 | FIRSTFLOOR_PLENUM ZN | 1660.73 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| 5 | MIDFLOOR_PLENUM ZN | 1660.73 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| 6 | PERIMETER_BOT_ZN_1 ZN | 207.34 | 11.2 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 7 | PERIMETER_BOT_ZN_2 ZN | 131.26 | 7.1 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 8 | PERIMETER_BOT_ZN_3 ZN | 207.34 | 11.2 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 9 | PERIMETER_BOT_ZN_4 ZN | 131.25 | 7.1 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 10 | PERIMETER_MID_ZN_1 ZN | 207.34 | 11.2 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 11 | PERIMETER_MID_ZN_2 ZN | 131.26 | 7.1 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 12 | PERIMETER_MID_ZN_3 ZN | 207.34 | 11.2 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 13 | PERIMETER_MID_ZN_4 ZN | 131.25 | 7.1 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 14 | PERIMETER_TOP_ZN_1 ZN | 207.34 | 11.2 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 15 | PERIMETER_TOP_ZN_2 ZN | 131.26 | 7.1 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 16 | PERIMETER_TOP_ZN_3 ZN | 207.34 | 11.2 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 17 | PERIMETER_TOP_ZN_4 ZN | 131.25 | 7.1 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 18 | TOPFLOOR_PLENUM ZN | 1660.73 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Number of People {} | People/Floor Area {person/m2} | Floor Area per person {m2/person} | Fraction Radiant | Fraction Convected | Sensible Fraction Calculation | Activity level | ASHRAE 55 Warnings | Carbon Dioxide Generation Rate | Nominal Minimum Number of People | Nominal Maximum Number of People | |
| 1 | CORE_BOTTOM ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | CORE_BOTTOM ZN | 983.54 | 52.9 | 52.9 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 53 |
| 2 | CORE_MID ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | CORE_MID ZN | 983.54 | 52.9 | 52.9 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 53 |
| 3 | CORE_TOP ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | CORE_TOP ZN | 983.54 | 52.9 | 52.9 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 53 |
| 4 | PERIMETER_BOT_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_BOT_ZN_1 ZN | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 |
| 5 | PERIMETER_BOT_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_BOT_ZN_2 ZN | 131.26 | 7.1 | 7.1 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 |
| 6 | PERIMETER_BOT_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_BOT_ZN_3 ZN | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 |
| 7 | PERIMETER_BOT_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_BOT_ZN_4 ZN | 131.25 | 7.1 | 7.1 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 |
| 8 | PERIMETER_MID_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_MID_ZN_1 ZN | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 |
| 9 | PERIMETER_MID_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_MID_ZN_2 ZN | 131.26 | 7.1 | 7.1 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 |
| 10 | PERIMETER_MID_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_MID_ZN_3 ZN | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 |
| 11 | PERIMETER_MID_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_MID_ZN_4 ZN | 131.25 | 7.1 | 7.1 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 |
| 12 | PERIMETER_TOP_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_TOP_ZN_1 ZN | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 |
| 13 | PERIMETER_TOP_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_TOP_ZN_2 ZN | 131.26 | 7.1 | 7.1 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 |
| 14 | PERIMETER_TOP_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_TOP_ZN_3 ZN | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 |
| 15 | PERIMETER_TOP_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_TOP_ZN_4 ZN | 131.25 | 7.1 | 7.1 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Lighting Level {W} | Lights/Floor Area {W/m2} | Lights per person {W/person} | Fraction Return Air | Fraction Radiant | Fraction Short Wave | Fraction Convected | Fraction Replaceable | End-Use Category | Nominal Minimum Lighting Level {W} | Nominal Maximum Lighting Level {W} | |
| 1 | CORE_BOTTOM ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | CORE_BOTTOM ZN | 983.54 | 52.9 | 8681.094 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 8681.094 |
| 2 | CORE_MID ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | CORE_MID ZN | 983.54 | 52.9 | 8681.094 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 8681.094 |
| 3 | CORE_TOP ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | CORE_TOP ZN | 983.54 | 52.9 | 8681.094 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 8681.094 |
| 4 | PERIMETER_BOT_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_BOT_ZN_1 ZN | 207.34 | 11.2 | 1830.051 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1830.051 |
| 5 | PERIMETER_BOT_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_BOT_ZN_2 ZN | 131.26 | 7.1 | 1158.573 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1158.573 |
| 6 | PERIMETER_BOT_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_BOT_ZN_3 ZN | 207.34 | 11.2 | 1830.051 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1830.051 |
| 7 | PERIMETER_BOT_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_BOT_ZN_4 ZN | 131.25 | 7.1 | 1158.497 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1158.497 |
| 8 | PERIMETER_MID_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_MID_ZN_1 ZN | 207.34 | 11.2 | 1830.051 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1830.051 |
| 9 | PERIMETER_MID_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_MID_ZN_2 ZN | 131.26 | 7.1 | 1158.573 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1158.573 |
| 10 | PERIMETER_MID_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_MID_ZN_3 ZN | 207.34 | 11.2 | 1830.051 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1830.051 |
| 11 | PERIMETER_MID_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_MID_ZN_4 ZN | 131.25 | 7.1 | 1158.497 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1158.497 |
| 12 | PERIMETER_TOP_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_TOP_ZN_1 ZN | 207.34 | 11.2 | 1830.051 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1830.051 |
| 13 | PERIMETER_TOP_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_TOP_ZN_2 ZN | 131.26 | 7.1 | 1158.573 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1158.573 |
| 14 | PERIMETER_TOP_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_TOP_ZN_3 ZN | 207.34 | 11.2 | 1830.051 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1830.051 |
| 15 | PERIMETER_TOP_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_TOP_ZN_4 ZN | 131.25 | 7.1 | 1158.497 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1158.497 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Equipment Level {W} | Equipment/Floor Area {W/m2} | Equipment per person {W/person} | Fraction Latent | Fraction Radiant | Fraction Lost | Fraction Convected | End-Use SubCategory | Nominal Minimum Equipment Level {W} | Nominal Maximum Equipment Level {W} | |
| 1 | 2 ELEVATOR FANS | OFFICEMEDIUM ELEV_LIGHT_FAN_SCH_ADD_DF | CORE_BOTTOM ZN | 983.54 | 52.9 | 61.915 | 6.295E-002 | 1.170 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 42.721 |
| 2 | 2 ELEVATOR LIFT MOTORS | OFFICEMEDIUM BLDG_ELEVATORS | CORE_BOTTOM ZN | 983.54 | 52.9 | 32110.000 | 32.647 | 606.610 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 22155.900 |
| 3 | 2 ELEVATOR LIGHTS | OFFICEMEDIUM ELEV_LIGHT_FAN_SCH_ADD_DF | CORE_BOTTOM ZN | 983.54 | 52.9 | 64.697 | 6.578E-002 | 1.222 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 44.641 |
| 4 | CORE_BOTTOM ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | CORE_BOTTOM ZN | 983.54 | 52.9 | 7940.025 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 7940.025 |
| 5 | CORE_MID ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | CORE_MID ZN | 983.54 | 52.9 | 7940.025 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 7940.025 |
| 6 | CORE_TOP ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | CORE_TOP ZN | 983.54 | 52.9 | 7940.025 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 7940.025 |
| 7 | PERIMETER_BOT_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_BOT_ZN_1 ZN | 207.34 | 11.2 | 1673.827 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1673.827 |
| 8 | PERIMETER_BOT_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_BOT_ZN_2 ZN | 131.26 | 7.1 | 1059.671 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1059.671 |
| 9 | PERIMETER_BOT_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_BOT_ZN_3 ZN | 207.34 | 11.2 | 1673.827 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1673.827 |
| 10 | PERIMETER_BOT_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_BOT_ZN_4 ZN | 131.25 | 7.1 | 1059.601 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1059.601 |
| 11 | PERIMETER_MID_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_MID_ZN_1 ZN | 207.34 | 11.2 | 1673.827 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1673.827 |
| 12 | PERIMETER_MID_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_MID_ZN_2 ZN | 131.26 | 7.1 | 1059.671 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1059.671 |
| 13 | PERIMETER_MID_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_MID_ZN_3 ZN | 207.34 | 11.2 | 1673.827 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1673.827 |
| 14 | PERIMETER_MID_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_MID_ZN_4 ZN | 131.25 | 7.1 | 1059.601 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1059.601 |
| 15 | PERIMETER_TOP_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_TOP_ZN_1 ZN | 207.34 | 11.2 | 1673.827 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1673.827 |
| 16 | PERIMETER_TOP_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_TOP_ZN_2 ZN | 131.26 | 7.1 | 1059.671 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1059.671 |
| 17 | PERIMETER_TOP_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_TOP_ZN_3 ZN | 207.34 | 11.2 | 1673.827 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1673.827 |
| 18 | PERIMETER_TOP_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_TOP_ZN_4 ZN | 131.25 | 7.1 | 1059.601 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1059.601 |
| Calculation Method | Value {days} | Allowable Number Figures in Shadow Overlap {} | Polygon Clipping Algorithm | Sky Diffuse Modeling Algorithm | External Shading Calculation Method | Output External Shading Calculation Results | Disable Self-Shading Within Shading Zone Groups | Disable Self-Shading From Shading Zone Groups to Other Zones | |
| 1 | AverageOverDaysInFrequency | 7 | 15000 | SutherlandHodgman | SimpleSkyDiffuseModeling | InternalCalculation | No | No | No |
| Zone Name | Number of Exterior Windows | Number of Exterior Windows in Adjacent Zones | |
| 1 | PERIMETER_BOT_ZN_1 ZN | 1 | 0 |
| 2 | PERIMETER_BOT_ZN_2 ZN | 1 | 0 |
| 3 | PERIMETER_BOT_ZN_3 ZN | 1 | 0 |
| 4 | PERIMETER_BOT_ZN_4 ZN | 1 | 0 |
| 5 | PERIMETER_MID_ZN_1 ZN | 1 | 0 |
| 6 | PERIMETER_MID_ZN_2 ZN | 1 | 0 |
| 7 | PERIMETER_MID_ZN_3 ZN | 1 | 0 |
| 8 | PERIMETER_MID_ZN_4 ZN | 1 | 0 |
| 9 | PERIMETER_TOP_ZN_1 ZN | 1 | 0 |
| 10 | PERIMETER_TOP_ZN_2 ZN | 1 | 0 |
| 11 | PERIMETER_TOP_ZN_3 ZN | 1 | 0 |
| 12 | PERIMETER_TOP_ZN_4 ZN | 1 | 0 |
| Zone Name | Number of Adjacent Zones with Windows | Adjacent Zone Names - 1st 100 (max) | |
| 1 | PERIMETER_BOT_ZN_1 ZN | 0 | |
| 2 | PERIMETER_BOT_ZN_2 ZN | 0 | |
| 3 | PERIMETER_BOT_ZN_3 ZN | 0 | |
| 4 | PERIMETER_BOT_ZN_4 ZN | 0 | |
| 5 | PERIMETER_MID_ZN_1 ZN | 0 | |
| 6 | PERIMETER_MID_ZN_2 ZN | 0 | |
| 7 | PERIMETER_MID_ZN_3 ZN | 0 | |
| 8 | PERIMETER_MID_ZN_4 ZN | 0 | |
| 9 | PERIMETER_TOP_ZN_1 ZN | 0 | |
| 10 | PERIMETER_TOP_ZN_2 ZN | 0 | |
| 11 | PERIMETER_TOP_ZN_3 ZN | 0 | |
| 12 | PERIMETER_TOP_ZN_4 ZN | 0 |
| Type | Name | Volume {m3} | Maximum Capacity {W} | Standard Rated Recovery Efficiency | Standard Rated Energy Factor | |
| 1 | WaterHeater:Mixed | 100GAL NATURAL GAS WATER HEATER - 100KBTU/HR 0.802 THERM EFF 0.808 THERM EFF | 0.3785 | 29307.1 | 1.016 | 0.2254 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Design Volume Flow Rate {m3/s} | Volume Flow Rate/Floor Area {m3/s-m2} | Volume Flow Rate/Exterior Surface Area {m3/s-m2} | ACH - Air Changes per Hour | Equation A - Constant Term Coefficient {} | Equation B - Temperature Term Coefficient {1/C} | Equation C - Velocity Term Coefficient {s/m} | Equation D - Velocity Squared Term Coefficient {s2/m2} | |
| 1 | FIRSTFLOOR_PLENUM INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | FIRSTFLOOR_PLENUM ZN | 1660.73 | 0.0 | 0.116 | 6.957E-005 | 5.696E-004 | 0.205 | 0.000 | 0.000 | 0.224 | 0.000 |
| 2 | MIDFLOOR_PLENUM INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | MIDFLOOR_PLENUM ZN | 1660.73 | 0.0 | 0.116 | 6.957E-005 | 5.696E-004 | 0.205 | 0.000 | 0.000 | 0.224 | 0.000 |
| 3 | ENTRY DOOR INFILTRATION | OFFICEMEDIUM INFIL_DOOR_OPENING_SCH | PERIMETER_BOT_ZN_1 ZN | 207.34 | 11.2 | 0.679 | 3.273E-003 | 4.957E-003 | 4.296 | 1.000 | 0.000 | 0.000 | 0.000 |
| 4 | PERIMETER_BOT_ZN_1 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_BOT_ZN_1 ZN | 207.34 | 11.2 | 7.798E-002 | 3.761E-004 | 5.696E-004 | 0.494 | 0.000 | 0.000 | 0.224 | 0.000 |
| 5 | PERIMETER_BOT_ZN_2 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_BOT_ZN_2 ZN | 131.26 | 7.1 | 5.199E-002 | 3.961E-004 | 5.696E-004 | 0.520 | 0.000 | 0.000 | 0.224 | 0.000 |
| 6 | PERIMETER_BOT_ZN_3 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_BOT_ZN_3 ZN | 207.34 | 11.2 | 7.798E-002 | 3.761E-004 | 5.696E-004 | 0.494 | 0.000 | 0.000 | 0.224 | 0.000 |
| 7 | PERIMETER_BOT_ZN_4 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_BOT_ZN_4 ZN | 131.25 | 7.1 | 5.199E-002 | 3.961E-004 | 5.696E-004 | 0.520 | 0.000 | 0.000 | 0.224 | 0.000 |
| 8 | PERIMETER_MID_ZN_1 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_MID_ZN_1 ZN | 207.34 | 11.2 | 7.798E-002 | 3.761E-004 | 5.696E-004 | 0.494 | 0.000 | 0.000 | 0.224 | 0.000 |
| 9 | PERIMETER_MID_ZN_2 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_MID_ZN_2 ZN | 131.26 | 7.1 | 5.199E-002 | 3.961E-004 | 5.696E-004 | 0.520 | 0.000 | 0.000 | 0.224 | 0.000 |
| 10 | PERIMETER_MID_ZN_3 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_MID_ZN_3 ZN | 207.34 | 11.2 | 7.798E-002 | 3.761E-004 | 5.696E-004 | 0.494 | 0.000 | 0.000 | 0.224 | 0.000 |
| 11 | PERIMETER_MID_ZN_4 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_MID_ZN_4 ZN | 131.25 | 7.1 | 5.199E-002 | 3.961E-004 | 5.696E-004 | 0.520 | 0.000 | 0.000 | 0.224 | 0.000 |
| 12 | PERIMETER_TOP_ZN_1 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_TOP_ZN_1 ZN | 207.34 | 11.2 | 7.798E-002 | 3.761E-004 | 5.696E-004 | 0.494 | 0.000 | 0.000 | 0.224 | 0.000 |
| 13 | PERIMETER_TOP_ZN_2 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_TOP_ZN_2 ZN | 131.26 | 7.1 | 5.199E-002 | 3.961E-004 | 5.696E-004 | 0.520 | 0.000 | 0.000 | 0.224 | 0.000 |
| 14 | PERIMETER_TOP_ZN_3 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_TOP_ZN_3 ZN | 207.34 | 11.2 | 7.798E-002 | 3.761E-004 | 5.696E-004 | 0.494 | 0.000 | 0.000 | 0.224 | 0.000 |
| 15 | PERIMETER_TOP_ZN_4 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_TOP_ZN_4 ZN | 131.25 | 7.1 | 5.199E-002 | 3.961E-004 | 5.696E-004 | 0.520 | 0.000 | 0.000 | 0.224 | 0.000 |
| 16 | TOPFLOOR_PLENUM INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | TOPFLOOR_PLENUM ZN | 1660.73 | 0.0 | 0.116 | 6.957E-005 | 6.199E-005 | 0.205 | 0.000 | 0.000 | 0.224 | 0.000 |
| Simple | |
| 1 | Simple |
| Zone Name | Mixing/Mundt/UCSDDV/UCSDCV/UCSDUFI/UCSDUFE/User Defined | |
| 1 | CORE_BOTTOM ZN | Mixing/Well-Stirred |
| 2 | CORE_MID ZN | Mixing/Well-Stirred |
| 3 | CORE_TOP ZN | Mixing/Well-Stirred |
| 4 | FIRSTFLOOR_PLENUM ZN | Mixing/Well-Stirred |
| 5 | MIDFLOOR_PLENUM ZN | Mixing/Well-Stirred |
| 6 | PERIMETER_BOT_ZN_1 ZN | Mixing/Well-Stirred |
| 7 | PERIMETER_BOT_ZN_2 ZN | Mixing/Well-Stirred |
| 8 | PERIMETER_BOT_ZN_3 ZN | Mixing/Well-Stirred |
| 9 | PERIMETER_BOT_ZN_4 ZN | Mixing/Well-Stirred |
| 10 | PERIMETER_MID_ZN_1 ZN | Mixing/Well-Stirred |
| 11 | PERIMETER_MID_ZN_2 ZN | Mixing/Well-Stirred |
| 12 | PERIMETER_MID_ZN_3 ZN | Mixing/Well-Stirred |
| 13 | PERIMETER_MID_ZN_4 ZN | Mixing/Well-Stirred |
| 14 | PERIMETER_TOP_ZN_1 ZN | Mixing/Well-Stirred |
| 15 | PERIMETER_TOP_ZN_2 ZN | Mixing/Well-Stirred |
| 16 | PERIMETER_TOP_ZN_3 ZN | Mixing/Well-Stirred |
| 17 | PERIMETER_TOP_ZN_4 ZN | Mixing/Well-Stirred |
| 18 | TOPFLOOR_PLENUM ZN | Mixing/Well-Stirred |
| No Multizone or Distribution/Multizone with Distribution/Multizone without Distribution/Multizone with Distribution only during Fan Operation | |
| 1 | NoMultizoneOrDistribution |
| Sensible Heat Capacity Multiplier | Moisture Capacity Multiplier | Carbon Dioxide Capacity Multiplier | Generic Contaminant Capacity Multiplier | |
| 1 | 1.000 | 1.000 | 1.000 | 1.000 |
| Value | |
| 1 | 6 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.0000 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.0000 |
| Zone Name | Load Type | Calc Des Load {W} | User Des Load {W} | Calc Des Air Flow Rate {m3/s} | User Des Air Flow Rate {m3/s} | Design Day Name | Date/Time of Peak | Temperature at Peak {C} | Humidity Ratio at Peak {kgWater/kgDryAir} | Floor Area {m2} | # Occupants | Calc Outdoor Air Flow Rate {m3/s} | Calc DOAS Heat Addition Rate {W} | |
| 1 | CORE_BOTTOM ZN | Cooling | 42233.33124 | 42233.33124 | 3.11018 | 3.11018 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:00:00 | 25.53000 | 1.49611E-002 | 983.53657 | 52.93350 | 0.42469 | 0.00000 |
| 2 | CORE_BOTTOM ZN | Heating | 8100.28275 | 8100.28275 | 0.34883 | 0.42469 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -20.00000 | 6.49857E-004 | 983.53657 | 52.93350 | 0.42469 | 0.00000 |
| 3 | CORE_MID ZN | Cooling | 31250.73238 | 31250.73238 | 2.29921 | 2.29921 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:00:00 | 25.53000 | 1.49611E-002 | 983.53657 | 52.93350 | 0.42469 | 0.00000 |
| 4 | CORE_MID ZN | Heating | 14967.52632 | 14967.52632 | 0.64886 | 0.64886 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -20.00000 | 6.49857E-004 | 983.53657 | 52.93350 | 0.42469 | 0.00000 |
| 5 | CORE_TOP ZN | Cooling | 31569.07633 | 31569.07633 | 2.32281 | 2.32281 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:00:00 | 25.53000 | 1.49611E-002 | 983.53657 | 52.93350 | 0.42469 | 0.00000 |
| 6 | CORE_TOP ZN | Heating | 26958.89215 | 26958.89215 | 1.17387 | 1.17387 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -20.00000 | 6.49857E-004 | 983.53657 | 52.93350 | 0.42469 | 0.00000 |
| 7 | PERIMETER_BOT_ZN_1 ZN | Cooling | 10842.33215 | 10842.33215 | 0.80511 | 0.80511 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 13:00:00 | 32.77500 | 1.49611E-002 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 8 | PERIMETER_BOT_ZN_1 ZN | Heating | 8591.73860 | 8591.73860 | 0.37475 | 0.37475 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -20.00000 | 6.49857E-004 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 9 | PERIMETER_BOT_ZN_2 ZN | Cooling | 10706.54773 | 10706.54773 | 0.78945 | 0.78945 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:00:00 | 25.53000 | 1.49611E-002 | 131.26219 | 7.06447 | 5.66790E-002 | 0.00000 |
| 10 | PERIMETER_BOT_ZN_2 ZN | Heating | 5591.33426 | 5591.33426 | 0.24391 | 0.24391 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -20.00000 | 6.49857E-004 | 131.26219 | 7.06447 | 5.66790E-002 | 0.00000 |
| 11 | PERIMETER_BOT_ZN_3 ZN | Cooling | 6752.32688 | 6752.32688 | 0.50141 | 0.50141 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 14:30:00 | 33.30000 | 1.49611E-002 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 12 | PERIMETER_BOT_ZN_3 ZN | Heating | 8428.89526 | 8428.89526 | 0.36762 | 0.36762 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -20.00000 | 6.49857E-004 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 13 | PERIMETER_BOT_ZN_4 ZN | Cooling | 10763.95494 | 10763.95494 | 0.79929 | 0.79929 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 16:50:00 | 31.97000 | 1.49611E-002 | 131.25358 | 7.06401 | 5.66753E-002 | 0.00000 |
| 14 | PERIMETER_BOT_ZN_4 ZN | Heating | 5681.18340 | 5681.18340 | 0.24784 | 0.24784 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -20.00000 | 6.49857E-004 | 131.25358 | 7.06401 | 5.66753E-002 | 0.00000 |
| 15 | PERIMETER_MID_ZN_1 ZN | Cooling | 12389.08523 | 12389.08523 | 0.91997 | 0.91997 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 13:00:00 | 32.77500 | 1.49611E-002 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 16 | PERIMETER_MID_ZN_1 ZN | Heating | 10250.54818 | 10250.54818 | 0.44736 | 0.44736 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -20.00000 | 6.49857E-004 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 17 | PERIMETER_MID_ZN_2 ZN | Cooling | 11840.30300 | 11840.30300 | 0.87308 | 0.87308 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:00:00 | 25.53000 | 1.49611E-002 | 131.26219 | 7.06447 | 5.66790E-002 | 0.00000 |
| 18 | PERIMETER_MID_ZN_2 ZN | Heating | 6644.01219 | 6644.01219 | 0.28998 | 0.28998 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -20.00000 | 6.49857E-004 | 131.26219 | 7.06447 | 5.66790E-002 | 0.00000 |
| 19 | PERIMETER_MID_ZN_3 ZN | Cooling | 8227.15015 | 8227.15015 | 0.61092 | 0.61092 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 14:20:00 | 33.30000 | 1.49611E-002 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 20 | PERIMETER_MID_ZN_3 ZN | Heating | 10107.20148 | 10107.20148 | 0.44109 | 0.44109 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -20.00000 | 6.49857E-004 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 21 | PERIMETER_MID_ZN_4 ZN | Cooling | 11796.02270 | 11796.02270 | 0.87593 | 0.87593 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 16:50:00 | 31.97000 | 1.49611E-002 | 131.25358 | 7.06401 | 5.66753E-002 | 0.00000 |
| 22 | PERIMETER_MID_ZN_4 ZN | Heating | 6748.74085 | 6748.74085 | 0.29457 | 0.29457 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -20.00000 | 6.49857E-004 | 131.25358 | 7.06401 | 5.66753E-002 | 0.00000 |
| 23 | PERIMETER_TOP_ZN_1 ZN | Cooling | 13296.33953 | 13296.33953 | 0.98735 | 0.98735 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 13:10:00 | 32.86250 | 1.49611E-002 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 24 | PERIMETER_TOP_ZN_1 ZN | Heating | 12668.98733 | 12668.98733 | 0.55322 | 0.55322 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -20.00000 | 6.49857E-004 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 25 | PERIMETER_TOP_ZN_2 ZN | Cooling | 11863.44526 | 11863.44526 | 0.87481 | 0.87481 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:00:00 | 25.53000 | 1.49611E-002 | 131.26219 | 7.06447 | 5.66790E-002 | 0.00000 |
| 26 | PERIMETER_TOP_ZN_2 ZN | Heating | 8172.01397 | 8172.01397 | 0.35686 | 0.35686 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -20.00000 | 6.49857E-004 | 131.26219 | 7.06447 | 5.66790E-002 | 0.00000 |
| 27 | PERIMETER_TOP_ZN_3 ZN | Cooling | 9245.67133 | 9245.67133 | 0.68656 | 0.68656 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 14:40:00 | 33.30000 | 1.49611E-002 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 28 | PERIMETER_TOP_ZN_3 ZN | Heating | 12553.35572 | 12553.35572 | 0.54815 | 0.54815 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -20.00000 | 6.49857E-004 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 29 | PERIMETER_TOP_ZN_4 ZN | Cooling | 12411.93141 | 12411.93141 | 0.92167 | 0.92167 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 16:40:00 | 32.11000 | 1.49611E-002 | 131.25358 | 7.06401 | 5.66753E-002 | 0.00000 |
| 30 | PERIMETER_TOP_ZN_4 ZN | Heating | 8280.64373 | 8280.64373 | 0.36162 | 0.36162 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -20.00000 | 6.49857E-004 | 131.25358 | 7.06401 | 5.66753E-002 | 0.00000 |
| System Name | Load Type | Peak Load Kind | User Design Capacity | Calc Des Air Flow Rate [m3/s] | User Des Air Flow Rate [m3/s] | Design Day Name | Date/Time of Peak | |
| 1 | 15 ZONE VAV | Cooling | Sensible | 219388.07 | 14.76359 | 14.76359 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 00:00:00 |
| 2 | 15 ZONE VAV | Heating | Sensible | 83320.48 | 6.77440 | 6.77440 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 23:00:00 |
| Component Type | Component Name | Input Field Description | Value | |
| 1 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 3.11018 |
| 2 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.24097 |
| 3 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 4 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 0.31102 |
| 5 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.64258 |
| 6 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 7 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.58112E-003 |
| 8 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 2.52399E-004 |
| 9 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.34883 |
| 10 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 11 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 12 | Coil:Heating:Water | CORE_BOTTOM ZN REHEAT COIL | Design Size Rated Capacity [W] | 11539.36264 |
| 13 | Coil:Heating:Water | CORE_BOTTOM ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 2.52399E-004 |
| 14 | Coil:Heating:Water | CORE_BOTTOM ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 837.18680 |
| 15 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 2.29921 |
| 16 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.32596 |
| 17 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 18 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 0.22992 |
| 19 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.86923 |
| 20 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 21 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.16885E-003 |
| 22 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 4.67304E-004 |
| 23 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.64886 |
| 24 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 25 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 26 | Coil:Heating:Water | CORE_MID ZN REHEAT COIL | Design Size Rated Capacity [W] | 21364.57123 |
| 27 | Coil:Heating:Water | CORE_MID ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 4.67304E-004 |
| 28 | Coil:Heating:Water | CORE_MID ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 1539.10121 |
| 29 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 2.32281 |
| 30 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.32265 |
| 31 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 32 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 0.23228 |
| 33 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.86040 |
| 34 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 35 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.18085E-003 |
| 36 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 8.42806E-004 |
| 37 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 1.17387 |
| 38 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 39 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 40 | Coil:Heating:Water | CORE_TOP ZN REHEAT COIL | Design Size Rated Capacity [W] | 38532.05768 |
| 41 | Coil:Heating:Water | CORE_TOP ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 8.42806E-004 |
| 42 | Coil:Heating:Water | CORE_TOP ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 2762.85764 |
| 43 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.80511 |
| 44 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.19624 |
| 45 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 46 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 8.05111E-002 |
| 47 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.52330 |
| 48 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 49 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.94154E-003 |
| 50 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 2.68705E-004 |
| 51 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.37475 |
| 52 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 53 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 54 | Coil:Heating:Water | PERIMETER_BOT_ZN_1 ZN REHEAT COIL | Design Size Rated Capacity [W] | 12284.87153 |
| 55 | Coil:Heating:Water | PERIMETER_BOT_ZN_1 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 2.68705E-004 |
| 56 | Coil:Heating:Water | PERIMETER_BOT_ZN_1 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 879.10463 |
| 57 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.78945 |
| 58 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.12670 |
| 59 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 60 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 7.89446E-002 |
| 61 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.33786 |
| 62 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 63 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 3.00713E-003 |
| 64 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 1.74874E-004 |
| 65 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.24391 |
| 66 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 67 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 68 | Coil:Heating:Water | PERIMETER_BOT_ZN_2 ZN REHEAT COIL | Design Size Rated Capacity [W] | 7995.00671 |
| 69 | Coil:Heating:Water | PERIMETER_BOT_ZN_2 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 1.74874E-004 |
| 70 | Coil:Heating:Water | PERIMETER_BOT_ZN_2 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 572.06703 |
| 71 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.50141 |
| 72 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.31510 |
| 73 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 74 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 5.01406E-002 |
| 75 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.84026 |
| 76 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 77 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.20915E-003 |
| 78 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 2.63605E-004 |
| 79 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.36762 |
| 80 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 81 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 82 | Coil:Heating:Water | PERIMETER_BOT_ZN_3 ZN REHEAT COIL | Design Size Rated Capacity [W] | 12051.69624 |
| 83 | Coil:Heating:Water | PERIMETER_BOT_ZN_3 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 2.63605E-004 |
| 84 | Coil:Heating:Water | PERIMETER_BOT_ZN_3 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 862.47580 |
| 85 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.79929 |
| 86 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.12513 |
| 87 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 88 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 7.99286E-002 |
| 89 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.33368 |
| 90 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 91 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 3.04481E-003 |
| 92 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 1.77688E-004 |
| 93 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.24784 |
| 94 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 95 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 96 | Coil:Heating:Water | PERIMETER_BOT_ZN_4 ZN REHEAT COIL | Design Size Rated Capacity [W] | 8123.66142 |
| 97 | Coil:Heating:Water | PERIMETER_BOT_ZN_4 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 1.77688E-004 |
| 98 | Coil:Heating:Water | PERIMETER_BOT_ZN_4 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 581.24104 |
| 99 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.91997 |
| 100 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.17174 |
| 101 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 102 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 9.19973E-002 |
| 103 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.45796 |
| 104 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 105 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 2.21853E-003 |
| 106 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 3.20639E-004 |
| 107 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.44736 |
| 108 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 109 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 110 | Coil:Heating:Water | PERIMETER_MID_ZN_1 ZN REHEAT COIL | Design Size Rated Capacity [W] | 14659.21299 |
| 111 | Coil:Heating:Water | PERIMETER_MID_ZN_1 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 3.20639E-004 |
| 112 | Coil:Heating:Water | PERIMETER_MID_ZN_1 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 1048.37925 |
| 113 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.87308 |
| 114 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.11456 |
| 115 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 116 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 8.73075E-002 |
| 117 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.30550 |
| 118 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 119 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 3.32569E-003 |
| 120 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 2.07830E-004 |
| 121 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.28998 |
| 122 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 123 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 124 | Coil:Heating:Water | PERIMETER_MID_ZN_2 ZN REHEAT COIL | Design Size Rated Capacity [W] | 9501.72021 |
| 125 | Coil:Heating:Water | PERIMETER_MID_ZN_2 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 2.07830E-004 |
| 126 | Coil:Heating:Water | PERIMETER_MID_ZN_2 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 679.48312 |
| 127 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.61092 |
| 128 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.25861 |
| 129 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 130 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 6.10925E-002 |
| 131 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.68963 |
| 132 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 133 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.47326E-003 |
| 134 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 3.16150E-004 |
| 135 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.44109 |
| 136 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 137 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 138 | Coil:Heating:Water | PERIMETER_MID_ZN_3 ZN REHEAT COIL | Design Size Rated Capacity [W] | 14453.98554 |
| 139 | Coil:Heating:Water | PERIMETER_MID_ZN_3 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 3.16150E-004 |
| 140 | Coil:Heating:Water | PERIMETER_MID_ZN_3 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 1033.74451 |
| 141 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.87593 |
| 142 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.11418 |
| 143 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 144 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 8.75929E-002 |
| 145 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.30449 |
| 146 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 147 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 3.33678E-003 |
| 148 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 2.11109E-004 |
| 149 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.29457 |
| 150 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 151 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 152 | Coil:Heating:Water | PERIMETER_MID_ZN_4 ZN REHEAT COIL | Design Size Rated Capacity [W] | 9651.66147 |
| 153 | Coil:Heating:Water | PERIMETER_MID_ZN_4 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 2.11109E-004 |
| 154 | Coil:Heating:Water | PERIMETER_MID_ZN_4 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 690.17418 |
| 155 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.98735 |
| 156 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.16002 |
| 157 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 158 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 9.87346E-002 |
| 159 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.42671 |
| 160 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 161 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 2.38100E-003 |
| 162 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 3.96359E-004 |
| 163 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.55322 |
| 164 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 165 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 166 | Coil:Heating:Water | PERIMETER_TOP_ZN_1 ZN REHEAT COIL | Design Size Rated Capacity [W] | 18121.05856 |
| 167 | Coil:Heating:Water | PERIMETER_TOP_ZN_1 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 3.96359E-004 |
| 168 | Coil:Heating:Water | PERIMETER_TOP_ZN_1 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 1295.24643 |
| 169 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.87481 |
| 170 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.11434 |
| 171 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 172 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 8.74807E-002 |
| 173 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.30490 |
| 174 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 175 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 3.33229E-003 |
| 176 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 2.55670E-004 |
| 177 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.35686 |
| 178 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 179 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 180 | Coil:Heating:Water | PERIMETER_TOP_ZN_2 ZN REHEAT COIL | Design Size Rated Capacity [W] | 11688.93449 |
| 181 | Coil:Heating:Water | PERIMETER_TOP_ZN_2 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 2.55670E-004 |
| 182 | Coil:Heating:Water | PERIMETER_TOP_ZN_2 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 835.45412 |
| 183 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.68656 |
| 184 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.23012 |
| 185 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 186 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 6.86559E-002 |
| 187 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.61366 |
| 188 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 189 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.65565E-003 |
| 190 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 3.92738E-004 |
| 191 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.54815 |
| 192 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 193 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 194 | Coil:Heating:Water | PERIMETER_TOP_ZN_3 ZN REHEAT COIL | Design Size Rated Capacity [W] | 17955.52190 |
| 195 | Coil:Heating:Water | PERIMETER_TOP_ZN_3 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 3.92738E-004 |
| 196 | Coil:Heating:Water | PERIMETER_TOP_ZN_3 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 1283.44252 |
| 197 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.92167 |
| 198 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.10852 |
| 199 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 200 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 9.21668E-002 |
| 201 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.30000 |
| 202 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 203 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 3.51102E-003 |
| 204 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 2.59072E-004 |
| 205 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.36162 |
| 206 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 207 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 208 | Coil:Heating:Water | PERIMETER_TOP_ZN_4 ZN REHEAT COIL | Design Size Rated Capacity [W] | 11844.45025 |
| 209 | Coil:Heating:Water | PERIMETER_TOP_ZN_4 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 2.59072E-004 |
| 210 | Coil:Heating:Water | PERIMETER_TOP_ZN_4 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 846.54240 |
| 211 | AirLoopHVAC | 15 ZONE VAV | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 8.68887 |
| 212 | AirLoopHVAC | 15 ZONE VAV | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 1.73777 |
| 213 | AirLoopHVAC | 15 ZONE VAV | Sum of Air Terminal Maximum Flow Rates [m3/s] | 17.37773 |
| 214 | AirLoopHVAC | 15 ZONE VAV | Adjusted Heating Design Air Flow Rate [m3/s] | 6.77440 |
| 215 | AirLoopHVAC | 15 ZONE VAV | Adjusted Cooling Design Air Flow Rate [m3/s] | 14.76359 |
| 216 | AirLoopHVAC | 15 ZONE VAV | Adjusted Main Design Air Flow Rate [m3/s] | 14.76359 |
| 217 | AirLoopHVAC | 15 ZONE VAV | User Heating Air Flow Ratio [] | 0.30000 |
| 218 | AirLoopHVAC | 15 ZONE VAV | Calculated Heating Air Flow Ratio [] | 0.45886 |
| 219 | AirLoopHVAC | 15 ZONE VAV | Design Supply Air Flow Rate [m3/s] | 14.76359 |
| 220 | Controller:OutdoorAir | 15 ZONE VAV OA CONTROLLER | Maximum Outdoor Air Flow Rate [m3/s] | 14.76359 |
| 221 | HeatExchanger:AirToAir:SensibleAndLatent | 15 ZONE VAV ERV | Design Size Nominal Supply Air Flow Rate [m3/s] | 2.15131 |
| 222 | Coil:Cooling:DX:TwoSpeed | 15 ZONE VAV 2SPD DX CLG COIL | Design Size High Speed Rated Air Flow Rate [m3/s] | 14.76359 |
| 223 | Coil:Cooling:DX:TwoSpeed | 15 ZONE VAV 2SPD DX CLG COIL | Design Size High Speed Gross Rated Total Cooling Capacity [W] |<PHONE_NUMBER>2 |
| 224 | Coil:Cooling:DX:TwoSpeed | 15 ZONE VAV 2SPD DX CLG COIL | Design Size High Speed Rated Sensible Heat Ratio | 0.76744 |
| 225 | Coil:Cooling:DX:TwoSpeed | 15 ZONE VAV 2SPD DX CLG COIL | Design Size Low Speed Rated Air Flow Rate [m3/s] | 4.92070 |
| 226 | Coil:Cooling:DX:TwoSpeed | 15 ZONE VAV 2SPD DX CLG COIL | Design Size Low Speed Gross Rated Total Cooling Capacity [W] | 99679.96814 |
| 227 | Coil:Cooling:DX:TwoSpeed | 15 ZONE VAV 2SPD DX CLG COIL | Design Size Low Speed Gross Rated Sensible Heat Ratio | 0.76744 |
| 228 | Coil:Cooling:DX:TwoSpeed | 15 ZONE VAV 2SPD DX CLG COIL | User-Specified Low Speed Gross Rated Sensible Heat Ratio | 0.69000 |
| 229 | Coil:Heating:Water | 15 ZONE VAV MAIN HTG COIL | Design Size Rated Capacity [W] | 63968.65546 |
| 230 | Coil:Heating:Water | 15 ZONE VAV MAIN HTG COIL | Design Size Maximum Water Flow Rate [m3/s] | 1.39918E-003 |
| 231 | Coil:Heating:Water | 15 ZONE VAV MAIN HTG COIL | Design Size U-Factor Times Area Value [W/K] | 1855.28675 |
| 232 | Fan:VariableVolume | 15 ZONE VAV FAN | Design Size Maximum Flow Rate [m3/s] | 14.76359 |
| 233 | Controller:WaterCoil | 15 ZONE VAV MAIN HTG COIL CONTROLLER | Maximum Actuated Flow [m3/s] | 1.39918E-003 |
| 234 | PlantLoop | HOT WATER LOOP | Maximum Loop Flow Rate [m3/s] | 6.20612E-003 |
| 235 | PlantLoop | HOT WATER LOOP | Plant Loop Volume [m3] | 0.74473 |
| 236 | Pump:VariableSpeed | HOT WATER LOOP PUMP | Design Flow Rate [m3/s] | 6.20612E-003 |
| 237 | Pump:VariableSpeed | HOT WATER LOOP PUMP | Design Power Consumption [W] | 1869.01160 |
| 238 | Boiler:HotWater | BOILER 968KBTU/HR 0.94 COMBUSTION EFF | Design Size Nominal Capacity [W] |<PHONE_NUMBER>3 |
| 239 | Boiler:HotWater | BOILER 968KBTU/HR 0.94 COMBUSTION EFF | Design Size Design Water Flow Rate [m3/s] | 6.20612E-003 |
| 240 | PlantLoop | MAIN SERVICE WATER LOOP | Maximum Loop Flow Rate [m3/s] | 5.36265E-005 |
| 241 | PlantLoop | MAIN SERVICE WATER LOOP | Plant Loop Volume [m3] | 6.43518E-003 |
| 242 | Pump:ConstantSpeed | SERVICE WATER LOOP PUMP | Design Flow Rate [m3/s] | 5.36265E-005 |
| 243 | Pump:ConstantSpeed | SERVICE WATER LOOP PUMP | Design Power Consumption [W] | 16.14994 |
| 244 | WaterHeater:Mixed | 100GAL NATURAL GAS WATER HEATER - 100KBTU/HR 0.802 THERM EFF 0.808 THERM EFF | Use Side Design Flow Rate [m3/s] | 5.36265E-005 |
| Component Type | Name | Nominal Total Capacity {W} | |
| 1 | Coil:Heating:Water | CORE_BOTTOM ZN REHEAT COIL | 20985.17 |
| 2 | Coil:Heating:Water | CORE_MID ZN REHEAT COIL | 38855.17 |
| 3 | Coil:Heating:Water | CORE_TOP ZN REHEAT COIL | 70078.05 |
| 4 | Coil:Heating:Water | PERIMETER_BOT_ZN_1 ZN REHEAT COIL | 22342.55 |
| 5 | Coil:Heating:Water | PERIMETER_BOT_ZN_2 ZN REHEAT COIL | 14540.56 |
| 6 | Coil:Heating:Water | PERIMETER_BOT_ZN_3 ZN REHEAT COIL | 21918.47 |
| 7 | Coil:Heating:Water | PERIMETER_BOT_ZN_4 ZN REHEAT COIL | 14774.55 |
| 8 | Coil:Heating:Water | PERIMETER_MID_ZN_1 ZN REHEAT COIL | 26660.82 |
| 9 | Coil:Heating:Water | PERIMETER_MID_ZN_2 ZN REHEAT COIL | 17280.85 |
| 10 | Coil:Heating:Water | PERIMETER_MID_ZN_3 ZN REHEAT COIL | 26287.57 |
| 11 | Coil:Heating:Water | PERIMETER_MID_ZN_4 ZN REHEAT COIL | 17553.55 |
| 12 | Coil:Heating:Water | PERIMETER_TOP_ZN_1 ZN REHEAT COIL | 32956.95 |
| 13 | Coil:Heating:Water | PERIMETER_TOP_ZN_2 ZN REHEAT COIL | 21258.79 |
| 14 | Coil:Heating:Water | PERIMETER_TOP_ZN_3 ZN REHEAT COIL | 32655.89 |
| 15 | Coil:Heating:Water | PERIMETER_TOP_ZN_4 ZN REHEAT COIL | 21541.63 |
| 16 | Coil:Heating:Water | 15 ZONE VAV MAIN HTG COIL | 87205.33 |
| DX Coil Type | DX Coil Name | Fan Type | Fan Name | Standard Net Cooling Capacity {W} | Standard Net Cooling Capacity {Btu/h} | IEER {Btu/W-h} | COP 100% Capacity {W/W} | COP 75% Capacity {W/W} | COP 50% Capacity {W/W} | COP 25% Capacity {W/W} | EER 100% Capacity {Btu/W-h} | EER 75% Capacity {Btu/W-h} | EER 50% Capacity {Btu/W-h} | EER 25% Capacity {Btu/W-h} | Supply Air Flow 100% {kg/s} | Supply Air Flow 75% {kg/s} | Supply Air Flow 50% {kg/s} | Supply Air Flow 25% {kg/s} | |
| 1 | Coil:Cooling:DX:TwoSpeed | 15 ZONE VAV 2SPD DX CLG COIL | N/A | N/A | 288159.60 | 983241.36 | 10.02 | 2.61 | 2.85 | 3.07 | 3.18 | 8.91 | 9.72 | 10.48 | 10.84 | 16.6730 | 12.3843 | 7.7571 | 3.4244 |
| Environment Name | Environment Type | Start Date | End Date | Start DayOfWeek | Duration {#days} | Source:Start DayOfWeek | Use Daylight Saving | Use Holidays | Apply Weekend Holiday Rule | Use Rain Values | Use Snow Values | |
| 1 | RUN PERIOD 1 | WeatherFileRunPeriod | 01/01/2006 | 12/31/2006 | Sunday | 365 | Use RunPeriod Specified Day | No | No | No | Yes | Yes |
| Daylight Saving Indicator | Source | Start Date | End Date | |
| 1 | Yes | InputFile | 03/12 | 11/05 |
| NumberofWarmupDays | |
| 1 | 10 |
| Style | Unit Conversion | |
| 1 | HTML | None |
| Zone Name | Environment Type/Name | Average Warmup Temperature Difference {deltaC} | Std Dev Warmup Temperature Difference {deltaC} | Max Temperature Pass/Fail Convergence | Min Temperature Pass/Fail Convergence | Average Warmup Load Difference {W} | Std Dev Warmup Load Difference {W} | Heating Load Pass/Fail Convergence | Cooling Load Pass/Fail Convergence | |
| 1 | CORE_BOTTOM ZN | RunPeriod: RUN PERIOD 1 | 4.8420945093E-002 | 2.8858223302E-002 | Pass | Pass | 0.4958098996 | 0.4962011297 | Pass | Pass |
| 2 | CORE_MID ZN | RunPeriod: RUN PERIOD 1 | 1.4177798899E-002 | 8.0021340912E-003 | Pass | Pass | 0.5252396956 | 0.5016952535 | Pass | Pass |
| 3 | CORE_TOP ZN | RunPeriod: RUN PERIOD 1 | 8.9192851236E-002 | 0.1066335469 | Pass | Pass | 13.0603747901 | 34.3773130869 | Pass | Pass |
| 4 | FIRSTFLOOR_PLENUM ZN | RunPeriod: RUN PERIOD 1 | 1.2092234099E-002 | 8.5450969230E-003 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 5 | MIDFLOOR_PLENUM ZN | RunPeriod: RUN PERIOD 1 | 1.3014430722E-002 | 1.0038368649E-002 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 6 | PERIMETER_BOT_ZN_1 ZN | RunPeriod: RUN PERIOD 1 | 0.1052587574 | 0.1163169340 | Pass | Pass | 0.9134157487 | 2.8213040754 | Pass | Pass |
| 7 | PERIMETER_BOT_ZN_2 ZN | RunPeriod: RUN PERIOD 1 | 7.8284942037E-002 | 8.5540574987E-002 | Pass | Pass | 2.0716581395 | 16.0712561270 | Pass | Pass |
| 8 | PERIMETER_BOT_ZN_3 ZN | RunPeriod: RUN PERIOD 1 | 3.4868765687E-002 | 3.7260939991E-002 | Pass | Pass | 0.7700025672 | 0.9606169376 | Pass | Pass |
| 9 | PERIMETER_BOT_ZN_4 ZN | RunPeriod: RUN PERIOD 1 | 6.1181450928E-002 | 6.1074348508E-002 | Pass | Pass | 0.8149158199 | 1.6603860520 | Pass | Pass |
| 10 | PERIMETER_MID_ZN_1 ZN | RunPeriod: RUN PERIOD 1 | 0.2069236786 | 0.2561235085 | Pass | Pass | 6.7347274019 | 39.2696870254 | Pass | Pass |
| 11 | PERIMETER_MID_ZN_2 ZN | RunPeriod: RUN PERIOD 1 | 0.2349222568 | 0.3034116168 | Pass | Pass |<PHONE_NUMBER>721 | 1012.9164959420 | Pass | Pass |
| 12 | PERIMETER_MID_ZN_3 ZN | RunPeriod: RUN PERIOD 1 | 0.2863726097 | 0.2995558712 | Pass | Pass |<PHONE_NUMBER>563 | 1015.9531712747 | Pass | Pass |
| 13 | PERIMETER_MID_ZN_4 ZN | RunPeriod: RUN PERIOD 1 | 0.3020111014 | 0.3459997535 | Pass | Pass | 23.5080274529 | 96.0172261084 | Pass | Pass |
| 14 | PERIMETER_TOP_ZN_1 ZN | RunPeriod: RUN PERIOD 1 | 0.3351685957 | 0.4189868558 | Pass | Pass | 32.1896421770 |<PHONE_NUMBER>187 | Pass | Pass |
| 15 | PERIMETER_TOP_ZN_2 ZN | RunPeriod: RUN PERIOD 1 | 0.4104289235 | 0.4716942405 | Pass | Pass | 18.3605348458 | 75.6953328548 | Pass | Pass |
| 16 | PERIMETER_TOP_ZN_3 ZN | RunPeriod: RUN PERIOD 1 | 0.4753885319 | 0.4622962694 | Pass | Pass | 26.4993673225 | 99.6898596588 | Pass | Pass |
| 17 | PERIMETER_TOP_ZN_4 ZN | RunPeriod: RUN PERIOD 1 | 0.4979356591 | 0.5246994907 | Pass | Pass | 19.4033277440 | 63.2118927553 | Pass | Pass |
| 18 | TOPFLOOR_PLENUM ZN | RunPeriod: RUN PERIOD 1 | 3.9048224186E-002 | 3.8016426007E-002 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
Report: Annual Heat Emissions Summary
For: Entire Facility
Timestamp: 2019-04-09 23:07:32
Heat Emission by Components| Envelope Convection | Zone Exfiltration | Zone Exhaust Air | HVAC Relief Air | HVAC Reject Heat | Total | |
| Heat Emissions [GJ] | 3178.82 | 149.53 | 0.00 | 1377.26 | 1105.91 | 5811.52 |
Report: Climatic Data Summary
For: Entire Facility
Timestamp: 2019-04-09 23:07:32
SizingPeriod:DesignDay| Maximum Dry Bulb [C] | Daily Temperature Range [deltaC] | Humidity Value | Humidity Type | Wind Speed [m/s] | Wind Direction | |
| CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 33.30 | 10.50 | 23.70 | Wetbulb [C] | 5.20 | 230.00 |
| CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | -20.00 | 0.00 | -20.00 | Wetbulb [C] | 4.90 | 270.00 |
| Value | |
| None |
Report: Envelope Summary
For: Entire Facility
Timestamp: 2019-04-09 23:07:32
Opaque Exterior| Construction | Reflectance | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Net Area [m2] | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| CORE_BOT_ZN_5_FLOOR | TYPICAL INSULATED CARPETED 8IN SLAB FLOOR | 0.30 | 2.144 | 3.285 | 983.54 | 983.54 | 0.00 | 180.00 | |
| PERIMETER_BOT_PLENUM_WALL_EAST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_BOT_PLENUM_WALL_NORTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_BOT_PLENUM_WALL_SOUTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_BOT_PLENUM_WALL_WEST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| PERIMETER_MID_PLENUM_WALL_EAST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_MID_PLENUM_WALL_NORTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_MID_PLENUM_WALL_SOUTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_MID_PLENUM_WALL_WEST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| PERIMETER_BOT_ZN_1_WALL_SOUTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_BOT_ZN_1_FLOOR | TYPICAL INSULATED CARPETED 8IN SLAB FLOOR | 0.30 | 2.144 | 3.285 | 207.34 | 207.34 | 0.00 | 180.00 | |
| PERIMETER_BOT_ZN_2_WALL_EAST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_BOT_ZN_2_FLOOR | TYPICAL INSULATED CARPETED 8IN SLAB FLOOR | 0.30 | 2.144 | 3.285 | 131.26 | 131.26 | 45.00 | 180.00 | |
| PERIMETER_BOT_ZN_3_WALL_NORTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_BOT_ZN_3_FLOOR | TYPICAL INSULATED CARPETED 8IN SLAB FLOOR | 0.30 | 2.144 | 3.285 | 207.34 | 207.34 | 0.00 | 180.00 | |
| PERIMETER_BOT_ZN_4_WALL_WEST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_BOT_ZN_4_FLOOR | TYPICAL INSULATED CARPETED 8IN SLAB FLOOR | 0.30 | 2.144 | 3.285 | 131.25 | 131.25 | 270.00 | 180.00 | |
| PERIMETER_MID_ZN_1_WALL_SOUTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_MID_ZN_2_WALL_EAST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_MID_ZN_3_WALL_NORTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_MID_ZN_4_WALL_WEST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_TOP_ZN_1_WALL_SOUTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_TOP_ZN_2_WALL_EAST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_TOP_ZN_3_WALL_NORTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_TOP_ZN_4_WALL_WEST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_TOP_PLENUM_WALL_EAST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_TOP_PLENUM_WALL_NORTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_TOP_PLENUM_WALL_SOUTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_TOP_PLENUM_WALL_WEST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-18.18 | 0.30 | 0.312 | 0.328 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| BUILDING_ROOF | TYPICAL IEAD ROOF R-31.25 | 0.30 | 0.182 | 0.186 | 1660.73 | 1660.73 | 0.00 | 0.00 |
| Construction | Glass Area [m2] | Frame Area [m2] | Divider Area [m2] | Area of One Opening [m2] | Area of Multiplied Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Frame Conductance [W/m2-K] | Divider Conductance [W/m2-K] | Shade Control | Parent Surface | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| PERIMETER_BOT_ZN_1_WALL_SOUTH_WINDOW | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 2.653 | 0.426 | 0.308 | No | PERIMETER_BOT_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_BOT_ZN_2_WALL_EAST_WINDOW | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 2.653 | 0.426 | 0.308 | No | PERIMETER_BOT_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_BOT_ZN_3_WALL_NORTH_WINDOW | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 2.653 | 0.426 | 0.308 | No | PERIMETER_BOT_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_BOT_ZN_4_WALL_WEST_WINDOW | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 2.653 | 0.426 | 0.308 | No | PERIMETER_BOT_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_MID_ZN_1_WALL_SOUTH_WINDOW | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 2.653 | 0.426 | 0.308 | No | PERIMETER_MID_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_MID_ZN_2_WALL_EAST_WINDOW | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 2.653 | 0.426 | 0.308 | No | PERIMETER_MID_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_MID_ZN_3_WALL_NORTH_WINDOW | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 2.653 | 0.426 | 0.308 | No | PERIMETER_MID_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_MID_ZN_4_WALL_WEST_WINDOW | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 2.653 | 0.426 | 0.308 | No | PERIMETER_MID_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_TOP_ZN_1_WALL_SOUTH_WINDOW | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 2.653 | 0.426 | 0.308 | No | PERIMETER_TOP_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_TOP_ZN_2_WALL_EAST_WINDOW | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 2.653 | 0.426 | 0.308 | No | PERIMETER_TOP_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_TOP_ZN_3_WALL_NORTH_WINDOW | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 2.653 | 0.426 | 0.308 | No | PERIMETER_TOP_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_TOP_ZN_4_WALL_WEST_WINDOW | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 2.653 | 0.426 | 0.308 | No | PERIMETER_TOP_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| Total or Average | 652.83 | 2.653 | 0.426 | 0.308 | ||||||||||||
| North Total or Average | 195.85 | 2.653 | 0.426 | 0.308 | ||||||||||||
| Non-North Total or Average | 456.98 | 2.653 | 0.426 | 0.308 |
| Construction | Area of One Opening [m2] | Area of Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Parent Surface | |
| Total or Average | 0.00 | - | - | - |
| Construction | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Parent Surface | |
| None |
Report: Shading Summary
For: Entire Facility
Timestamp: 2019-04-09 23:07:32
Sunlit Fraction| March 21 9am | March 21 noon | March 21 3pm | June 21 9am | June 21 noon | June 21 3pm | December 21 9am | December 21 noon | December 21 3pm | |
| PERIMETER_BOT_ZN_1_WALL_SOUTH_WINDOW | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 |
| PERIMETER_BOT_ZN_2_WALL_EAST_WINDOW | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 |
| PERIMETER_BOT_ZN_3_WALL_NORTH_WINDOW | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_4_WALL_WEST_WINDOW | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| PERIMETER_MID_ZN_1_WALL_SOUTH_WINDOW | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 |
| PERIMETER_MID_ZN_2_WALL_EAST_WINDOW | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 |
| PERIMETER_MID_ZN_3_WALL_NORTH_WINDOW | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_4_WALL_WEST_WINDOW | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| PERIMETER_TOP_ZN_1_WALL_SOUTH_WINDOW | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 |
| PERIMETER_TOP_ZN_2_WALL_EAST_WINDOW | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 |
| PERIMETER_TOP_ZN_3_WALL_NORTH_WINDOW | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_TOP_ZN_4_WALL_WEST_WINDOW | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| Name | Type | Shaded Construction | Control | Glare Control | |
| None |
Report: Lighting Summary
For: Entire Facility
Timestamp: 2019-04-09 23:07:32
Interior Lighting| Zone | Lighting Power Density [W/m2] | Zone Area [m2] | Total Power [W] | End Use Subcategory | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Return Air Fraction | Conditioned (Y/N) | Consumption [GJ] | |
| CORE_BOTTOM ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | CORE_BOTTOM ZN | 8.8264 | 983.54 | 8681.09 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 49.01 | 0.0000 | Y | 79.86 |
| CORE_MID ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | CORE_MID ZN | 8.8264 | 983.54 | 8681.09 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 49.01 | 0.0000 | Y | 79.86 |
| CORE_TOP ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | CORE_TOP ZN | 8.8264 | 983.54 | 8681.09 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 49.01 | 0.0000 | Y | 79.86 |
| PERIMETER_BOT_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_BOT_ZN_1 ZN | 8.8264 | 207.34 | 1830.05 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 28.93 | 0.0000 | Y | 9.94 |
| PERIMETER_BOT_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_BOT_ZN_2 ZN | 8.8264 | 131.26 | 1158.57 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 29.44 | 0.0000 | Y | 6.40 |
| PERIMETER_BOT_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_BOT_ZN_3 ZN | 8.8264 | 207.34 | 1830.05 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 29.75 | 0.0000 | Y | 10.22 |
| PERIMETER_BOT_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_BOT_ZN_4 ZN | 8.8264 | 131.25 | 1158.50 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 29.16 | 0.0000 | Y | 6.34 |
| PERIMETER_MID_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_MID_ZN_1 ZN | 8.8264 | 207.34 | 1830.05 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 28.87 | 0.0000 | Y | 9.92 |
| PERIMETER_MID_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_MID_ZN_2 ZN | 8.8264 | 131.26 | 1158.57 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 29.34 | 0.0000 | Y | 6.38 |
| PERIMETER_MID_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_MID_ZN_3 ZN | 8.8264 | 207.34 | 1830.05 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 29.59 | 0.0000 | Y | 10.16 |
| PERIMETER_MID_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_MID_ZN_4 ZN | 8.8264 | 131.25 | 1158.50 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 29.06 | 0.0000 | Y | 6.32 |
| PERIMETER_TOP_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_TOP_ZN_1 ZN | 8.8264 | 207.34 | 1830.05 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 28.87 | 0.0000 | Y | 9.92 |
| PERIMETER_TOP_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_TOP_ZN_2 ZN | 8.8264 | 131.26 | 1158.57 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 29.34 | 0.0000 | Y | 6.38 |
| PERIMETER_TOP_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_TOP_ZN_3 ZN | 8.8264 | 207.34 | 1830.05 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 29.59 | 0.0000 | Y | 10.16 |
| PERIMETER_TOP_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_TOP_ZN_4 ZN | 8.8264 | 131.25 | 1158.50 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 29.06 | 0.0000 | Y | 6.32 |
| Interior Lighting Total | 8.8264 | 4982.19 | 43974.80 | 338.04 |
| Zone | Control Name | Daylighting Method | Control Type | Fraction Controlled | Lighting Installed in Zone [W] | Lighting Controlled [W] | |
| PERIMETER_BOT_ZN_1 DAYLT SENSOR 1 | PERIMETER_BOT_ZN_1 ZN | PERIMETER_BOT_ZN_1 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1830.05 | 701.82 |
| PERIMETER_BOT_ZN_1 DAYLT SENSOR 2 | PERIMETER_BOT_ZN_1 ZN | PERIMETER_BOT_ZN_1 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1830.05 | 255.29 |
| PERIMETER_BOT_ZN_2 DAYLT SENSOR 1 | PERIMETER_BOT_ZN_2 ZN | PERIMETER_BOT_ZN_2 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1158.57 | 444.31 |
| PERIMETER_BOT_ZN_2 DAYLT SENSOR 2 | PERIMETER_BOT_ZN_2 ZN | PERIMETER_BOT_ZN_2 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1158.57 | 161.62 |
| PERIMETER_BOT_ZN_3 DAYLT SENSOR 1 | PERIMETER_BOT_ZN_3 ZN | PERIMETER_BOT_ZN_3 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1830.05 | 701.82 |
| PERIMETER_BOT_ZN_3 DAYLT SENSOR 2 | PERIMETER_BOT_ZN_3 ZN | PERIMETER_BOT_ZN_3 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1830.05 | 255.29 |
| PERIMETER_BOT_ZN_4 DAYLT SENSOR 1 | PERIMETER_BOT_ZN_4 ZN | PERIMETER_BOT_ZN_4 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1158.50 | 444.28 |
| PERIMETER_BOT_ZN_4 DAYLT SENSOR 2 | PERIMETER_BOT_ZN_4 ZN | PERIMETER_BOT_ZN_4 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1158.50 | 161.61 |
| PERIMETER_MID_ZN_1 DAYLT SENSOR 1 | PERIMETER_MID_ZN_1 ZN | PERIMETER_MID_ZN_1 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1830.05 | 701.82 |
| PERIMETER_MID_ZN_1 DAYLT SENSOR 2 | PERIMETER_MID_ZN_1 ZN | PERIMETER_MID_ZN_1 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1830.05 | 255.29 |
| PERIMETER_MID_ZN_2 DAYLT SENSOR 1 | PERIMETER_MID_ZN_2 ZN | PERIMETER_MID_ZN_2 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1158.57 | 444.31 |
| PERIMETER_MID_ZN_2 DAYLT SENSOR 2 | PERIMETER_MID_ZN_2 ZN | PERIMETER_MID_ZN_2 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1158.57 | 161.62 |
| PERIMETER_MID_ZN_3 DAYLT SENSOR 1 | PERIMETER_MID_ZN_3 ZN | PERIMETER_MID_ZN_3 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1830.05 | 701.82 |
| PERIMETER_MID_ZN_3 DAYLT SENSOR 2 | PERIMETER_MID_ZN_3 ZN | PERIMETER_MID_ZN_3 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1830.05 | 255.29 |
| PERIMETER_MID_ZN_4 DAYLT SENSOR 1 | PERIMETER_MID_ZN_4 ZN | PERIMETER_MID_ZN_4 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1158.50 | 444.28 |
| PERIMETER_MID_ZN_4 DAYLT SENSOR 2 | PERIMETER_MID_ZN_4 ZN | PERIMETER_MID_ZN_4 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1158.50 | 161.61 |
| PERIMETER_TOP_ZN_1 DAYLT SENSOR 1 | PERIMETER_TOP_ZN_1 ZN | PERIMETER_TOP_ZN_1 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1830.05 | 701.82 |
| PERIMETER_TOP_ZN_1 DAYLT SENSOR 2 | PERIMETER_TOP_ZN_1 ZN | PERIMETER_TOP_ZN_1 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1830.05 | 255.29 |
| PERIMETER_TOP_ZN_2 DAYLT SENSOR 1 | PERIMETER_TOP_ZN_2 ZN | PERIMETER_TOP_ZN_2 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1158.57 | 444.31 |
| PERIMETER_TOP_ZN_2 DAYLT SENSOR 2 | PERIMETER_TOP_ZN_2 ZN | PERIMETER_TOP_ZN_2 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1158.57 | 161.62 |
| PERIMETER_TOP_ZN_3 DAYLT SENSOR 1 | PERIMETER_TOP_ZN_3 ZN | PERIMETER_TOP_ZN_3 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1830.05 | 701.82 |
| PERIMETER_TOP_ZN_3 DAYLT SENSOR 2 | PERIMETER_TOP_ZN_3 ZN | PERIMETER_TOP_ZN_3 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1830.05 | 255.29 |
| PERIMETER_TOP_ZN_4 DAYLT SENSOR 1 | PERIMETER_TOP_ZN_4 ZN | PERIMETER_TOP_ZN_4 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1158.50 | 444.28 |
| PERIMETER_TOP_ZN_4 DAYLT SENSOR 2 | PERIMETER_TOP_ZN_4 ZN | PERIMETER_TOP_ZN_4 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1158.50 | 161.61 |
| Total Watts | Astronomical Clock/Schedule | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Consumption [GJ] | |
| NONDIMMING EXTERIOR LIGHTS DEF | 623.03 | AstronomicalClock | - | 42.70 | 42.70 | 4.99 | |
| OCC SENSING EXTERIOR LIGHTS DEF | 7476.45 | AstronomicalClock | - | 83.69 | 71.39 | 100.20 | |
| Exterior Lighting Total | 8099.48 | 105.19 |
Report: Equipment Summary
For: Entire Facility
Timestamp: 2019-04-09 23:07:32
Central Plant| Type | Nominal Capacity [W] | Nominal Efficiency [W/W] | IPLV in SI Units [W/W] | IPLV in IP Units [Btu/W-h] | |
| BOILER 968KBTU/HR 0.94 COMBUSTION EFF | Boiler:HotWater | 283736.43 | 0.93 |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Sensible Capacity [W] | Nominal Latent Capacity [W] | Nominal Sensible Heat Ratio | Nominal Efficiency [W/W] | Nominal Coil UA Value [W/C] | Nominal Coil Surface Area [m2] | |
| 15 ZONE VAV 2SPD DX CLG COIL | Coil:Cooling:DX:TwoSpeed | 299069.81 | 229516.81 | 69553.00 | 0.77 | 3.00 |
| DX Cooling Coil Type | Standard Rated Net Cooling Capacity [W] | Standard Rated Net COP [W/W] | EER [Btu/W-h] | SEER [Btu/W-h] | IEER [Btu/W-h] | |
| 15 ZONE VAV 2SPD DX CLG COIL | 288159.6 | 2.61 | 8.91 | N/A | 10.02 |
| DX Cooling Coil Type | Rated Net Cooling Capacity Test A [W] | Rated Electric Power Test A [W] | Rated Net Cooling Capacity Test B [W] | Rated Electric Power Test B [W] | Rated Net Cooling Capacity Test C [W] | Rated Electric Power Test C [W] | Rated Net Cooling Capacity Test D [W] | Rated Electric Power Test D [W] | |
| 15 ZONE VAV 2SPD DX CLG COIL | Coil:Cooling:DX:TwoSpeed |
| DX Heating Coil Type | High Temperature Heating (net) Rating Capacity [W] | Low Temperature Heating (net) Rating Capacity [W] | HSPF [Btu/W-h] | Region Number | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Efficiency [W/W] | |
| CORE_BOTTOM ZN REHEAT COIL | Coil:Heating:Water | 11539.36 | 20985.17 | - |
| CORE_MID ZN REHEAT COIL | Coil:Heating:Water | 21364.57 | 38855.17 | - |
| CORE_TOP ZN REHEAT COIL | Coil:Heating:Water | 38532.06 | 70078.05 | - |
| PERIMETER_BOT_ZN_1 ZN REHEAT COIL | Coil:Heating:Water | 12284.87 | 22342.55 | - |
| PERIMETER_BOT_ZN_2 ZN REHEAT COIL | Coil:Heating:Water | 7995.01 | 14540.56 | - |
| PERIMETER_BOT_ZN_3 ZN REHEAT COIL | Coil:Heating:Water | 12051.70 | 21918.47 | - |
| PERIMETER_BOT_ZN_4 ZN REHEAT COIL | Coil:Heating:Water | 8123.66 | 14774.55 | - |
| PERIMETER_MID_ZN_1 ZN REHEAT COIL | Coil:Heating:Water | 14659.21 | 26660.82 | - |
| PERIMETER_MID_ZN_2 ZN REHEAT COIL | Coil:Heating:Water | 9501.72 | 17280.85 | - |
| PERIMETER_MID_ZN_3 ZN REHEAT COIL | Coil:Heating:Water | 14453.99 | 26287.57 | - |
| PERIMETER_MID_ZN_4 ZN REHEAT COIL | Coil:Heating:Water | 9651.66 | 17553.55 | - |
| PERIMETER_TOP_ZN_1 ZN REHEAT COIL | Coil:Heating:Water | 18121.06 | 32956.95 | - |
| PERIMETER_TOP_ZN_2 ZN REHEAT COIL | Coil:Heating:Water | 11688.93 | 21258.79 | - |
| PERIMETER_TOP_ZN_3 ZN REHEAT COIL | Coil:Heating:Water | 17955.52 | 32655.89 | - |
| PERIMETER_TOP_ZN_4 ZN REHEAT COIL | Coil:Heating:Water | 11844.45 | 21541.63 | - |
| 15 ZONE VAV MAIN HTG COIL | Coil:Heating:Water | 63968.66 | 87205.33 | - |
| Type | Total Efficiency [W/W] | Delta Pressure [pa] | Max Air Flow Rate [m3/s] | Rated Electric Power [W] | Rated Power Per Max Air Flow Rate [W-s/m3] | Motor Heat In Air Fraction | Fan Energy Index | End Use Subcategory | Design Day Name for Fan Sizing Peak | Date/Time for Fan Sizing Peak | |
| 15 ZONE VAV FAN | Fan:VariableVolume | 0.64 | 996.36 | 14.76 | 22812.94 | 1545.22 | 1.00 | 1.20 | General | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 15:00:00 |
| Type | Control | Head [pa] | Water Flow [m3/s] | Electric Power [W] | Power Per Water Flow Rate [W-s/m3] | Motor Efficiency [W/W] | End Use Subcategory | |
| HOT WATER LOOP PUMP | Pump:VariableSpeed | Intermittent | 210237.10 | 0.006206 | 1869.01 | 301156.14 | 0.90 | General |
| SERVICE WATER LOOP PUMP | Pump:ConstantSpeed | Intermittent | 164431.25 | 0.000054 | 16.15 | 301156.14 | 0.70 | General |
| Type | Storage Volume [m3] | Input [W] | Thermal Efficiency [W/W] | Recovery Efficiency [W/W] | Energy Factor | |
| 100GAL NATURAL GAS WATER HEATER - 100KBTU/HR 0.802 THERM EFF 0.808 THERM EFF | WaterHeater:Mixed | 0.38 | 29307.11 | 0.81 | 1.02 | 0.23 |
| DX Cooling Coil Type | Assocated Fan | Net Cooling Capacity [W] | COP [W/W] | EER [Btu/W-h] | IEER [Btu/W-h] | Supply Air Flow 100% [kg/s] | COP 75% Capacity [W/W] | EER 75% Capacity [Btu/W-h] | Supply Air Flow 75% [kg/s] | COP 50% Capacity [W/W] | EER 50% Capacity [Btu/W-h] | Supply Air Flow 50% [kg/s] | COP 25% Capacity [W/W] | EER 25% Capacity [Btu/W-h] | Supply Air Flow 25% [kg/s] | |
| 15 ZONE VAV 2SPD DX CLG COIL | Coil:Cooling:DX:TwoSpeed | None | 288159.60 | 2.61 | 8.91 | 10.02 | 16.6730 | 2.85 | 9.72 | 12.3843 | 3.07 | 10.48 | 7.7571 | 3.18 | 10.84 | 3.4244 |
Report: HVAC Sizing Summary
For: Entire Facility
Timestamp: 2019-04-09 23:07:32
Zone Sensible Cooling| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| CORE_BOTTOM ZN | 42233.33 | 42233.33 | 42.94 | 3.110 | 3.110 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:00:00 | 24.00 | 24.00 | 0.00879 | 25.53 | 0.01496 | 0.425 | 0.00 |
| CORE_MID ZN | 31250.73 | 31250.73 | 31.77 | 2.299 | 2.299 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:00:00 | 24.00 | 24.00 | 0.00890 | 25.53 | 0.01496 | 0.425 | 0.00 |
| CORE_TOP ZN | 31569.08 | 31569.08 | 32.10 | 2.323 | 2.323 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:00:00 | 24.00 | 24.00 | 0.00889 | 25.53 | 0.01496 | 0.425 | 0.00 |
| PERIMETER_BOT_ZN_1 ZN | 10842.33 | 10842.33 | 52.29 | 0.805 | 0.805 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 13:00:00 | 24.00 | 24.00 | 0.00877 | 32.77 | 0.01496 | 0.090 | 0.00 |
| PERIMETER_BOT_ZN_2 ZN | 10706.55 | 10706.55 | 81.57 | 0.789 | 0.789 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:00:00 | 24.00 | 24.00 | 0.00868 | 25.53 | 0.01496 | 0.057 | 0.00 |
| PERIMETER_BOT_ZN_3 ZN | 6752.33 | 6752.33 | 32.57 | 0.501 | 0.501 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 14:30:00 | 24.00 | 24.00 | 0.00893 | 33.30 | 0.01496 | 0.090 | 0.00 |
| PERIMETER_BOT_ZN_4 ZN | 10763.95 | 10763.95 | 82.01 | 0.799 | 0.799 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 16:50:00 | 24.00 | 24.00 | 0.00867 | 31.97 | 0.01496 | 0.057 | 0.00 |
| PERIMETER_MID_ZN_1 ZN | 12389.09 | 12389.09 | 59.75 | 0.920 | 0.920 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 13:00:00 | 24.00 | 24.00 | 0.00876 | 32.77 | 0.01496 | 0.090 | 0.00 |
| PERIMETER_MID_ZN_2 ZN | 11840.30 | 11840.30 | 90.20 | 0.873 | 0.873 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:00:00 | 24.00 | 24.00 | 0.00867 | 25.53 | 0.01496 | 0.057 | 0.00 |
| PERIMETER_MID_ZN_3 ZN | 8227.15 | 8227.15 | 39.68 | 0.611 | 0.611 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 14:20:00 | 24.00 | 24.00 | 0.00888 | 33.30 | 0.01496 | 0.090 | 0.00 |
| PERIMETER_MID_ZN_4 ZN | 11796.02 | 11796.02 | 89.87 | 0.876 | 0.876 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 16:50:00 | 24.00 | 24.00 | 0.00867 | 31.97 | 0.01496 | 0.057 | 0.00 |
| PERIMETER_TOP_ZN_1 ZN | 13296.34 | 13296.34 | 64.13 | 0.987 | 0.987 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 13:10:00 | 24.00 | 24.00 | 0.00875 | 32.86 | 0.01496 | 0.090 | 0.00 |